I have used Greer's service for over 25 years and they have always delivered exceptional service! Would recommend them for all of your heating and air services!
very knowledgeable, thorough
Greer Service takes good care of it's customers. David is very knowledgeable and friendly. He gets the job done and helps you keep your costs down.
Accurate in diagnosis and cost estimate.
Solid, Honest, Reliable HVAC work. Did full A/C upsizing with duct-work and returns to renovated upstairs and smooth installation. Summer is about to start, so we'll see how that first hot season fares.
None of the big service names had any interest in repairing my older equipment, they just pushed expensive new replacements. I wasn't ready to upgrade, and fortunately my neighbor recommended that I call Greer. They kept my aging units going until there was more rust than metal, and finally I gave in and had them put in fancy new units at a fair price. I am very happy with the result and as claimed, they work better and use less electricity. Today my installation team came back out for our spring tune-up and it was like a reunion of old friends. I genuinely like these guys and if you enjoy doing business with competent, honest local folks who care, you will too.
Honest, trust-able, and reasonable, great company, great people
Serviced 2 Amana a/c units. Added 1-lb to the upstairs.
Repaired dun deteriorated wires in Trane condenser unit.
Completed spring Tune-ups to 3 Goodman A/c units. Cleaned coils and cleared drain lines. Added 1.5-lbs Puron to downstairs A/C and 1.5-lb Puron to the 2nd floor A/C. Adjusted charge for 3rd floor A/C.
Checked a Trane HP system. Reset the GFCI outside that controls the condensate pump. Pun is working fine. Re-ran drain line and installed a coupling and barb fitting (minor drain repair). Puron was good.
Conducted spring tune-up. Cleaned condenser coils, cleared drain lines, and checked refrigerant. All ok. The filters are in need of changing in the next week or so.
Conducted spring tune-up on 2 Lennox A/C’s. Cleaned condenser coils and added 1-lb Freon to the downstairs unit.
Conducted spring tube-up on an Amana has pack. Cleaned condenser coil.
Preformed maintenance on one Amana straight AC and a Carrier straight AC. Cleaned both outdoor coils and cleared both drains and checked wires and checked refrigerant everything was running like it is supposed too.
Preformed maintenance on a Amana Gas package unit. Cleaned outdoor coil, tightened wires, cleared drain, and checked refrigerant everything was running at its potential.
Found refrigerant valve leaking at suction line of Amana Heat Pump. Repaired it and filled unit with refrigerant.
Preformed maintenance on a 2003 trane straight AC unit. Cleaned outdoor coil, tightened wires, cleared drain and checked refrigerant all good.
Tune-up for an Amana hydro system.
Preformed maintenance on a 2015 and a 2017 Amana straight AC units. Checked refrigerant cleared drains tightened wires.
Preformed maintenance on 2 Goodman straight AC units. Cleaned coils cleared drains tightened wires and checked refrigerant all good.
Preformed maintenance on 2 2018 Amana straight AC units. Checked refrigerant, tightened wires and cleared drains.