Greer's helped me when I was really in a bind. They were compassionate and friendly as well as effective and efficient! I was told by another company that I completely needed a new system for about $6200. Greer's fixed it within an hour, for less than $100. Truly honest people who are good at what they do. I can't recommend them higher!!!
This was an excellent service call! I really appreciated how personal and professional the crew was. They took the time to explain what they were doing, what they found, and how they were fixing the problem. They also gave some very valuable maintenance tips. I HIGHLY recommend Greer's for all HVAC issues. They are our "go to" HVAC company.
Have always had good service. Very friendly and professional.
Polite, knowledgeable , helpful and hardworking
Technicians explained what they were doing and were prompt, friendly and put things back the way they were.
Love the Greer’s! Great company, honest people!
The service was great and the technicians were knowledgeable.
Dave was great. Called with timing updates. Arrived and got right to issue. Offer advice on future prep and longevity expectations
Greer came in and did an excellent job setting up our new unit. Would recommend the MBAs a profesional stand up company
They show up on time, do the job professionally, don't leave a mess, and leave with a smile.
Found safety switch keeping thermostat blank cleared drain and checked refrigerant
Had a tripped gfi on outlet that caused no power to condensate pump, pan float switch made the thermostat go blank. I got the water out of the pan and reset the gfi on outlet, it now works like it’s supposed too.
Checked A/C. Found drain clogged. Float switch had unit off. Cleared drain and checked system. All is ok.
Serviced Amana A/C and 2 mini split heat pumps. Cleaned outdoor coils. Added Puron to the main floor A/C unit
Preformed maintenance on a Lennox straight AC unit. Cleared drain, tightened wires, cleaned outdoor coil, and checked refrigerant all good.
Serviced Amanda heat pump. Checked drain. Checked Puron. Tightened wiring. Cleaned outdoor coil.
Serviced dual fuel system
The drains were clear and the pump worked for us. There’s an elbow that wasn’t glued and it looked to be dripping there. So, I glued that elbow and poured water down the drains. All worked perfectly.
Preformed maintenance on a 2015 Amana package unit. Cleaned outdoor coil, cleared drain, tightened wires, checked refrigerant all good.
Installed New HVAC System
Unstopped drain line. Installed a union. Installed new drain safety and vacuumed water out of drain pan
Advised owner about longevity of the current system.
Checked Lennox gas pack. Found 30/5/440 dual capacitor bad. Replaced capacitor and added 2-lbs Freon (R-22).
Installed a new Amana furnace and A/C system.
Checked Trane A/C. Found power off at switch in the attic to the furnace. Turned power switch on and then found unit low on Freon added 1-lb Freon (R-22).