teck showed up when supposed to ,preformed heating inspection . happy to deal with Greer
always great to work with
Greer's is a great company with a deep bench of professionals that know HVAC systems inside and out. They always come through to keep my equipment running smoothly. Their service and warranty cannot be beat.
Greer's helped me when I was really in a bind. They were compassionate and friendly as well as effective and efficient! I was told by another company that I completely needed a new system for about $6200. Greer's fixed it within an hour, for less than $100. Truly honest people who are good at what they do. I can't recommend them higher!!!
This was an excellent service call! I really appreciated how personal and professional the crew was. They took the time to explain what they were doing, what they found, and how they were fixing the problem. They also gave some very valuable maintenance tips. I HIGHLY recommend Greer's for all HVAC issues. They are our "go to" HVAC company.
Have always had good service. Very friendly and professional.
Polite, knowledgeable , helpful and hardworking
Technicians explained what they were doing and were prompt, friendly and put things back the way they were.
Love the Greer’s! Great company, honest people!
Serviced Lennox Pulse 90% GF,serviced Lennox 80%GF,took amps, tightened wiring,checked safeties,the only thing found wrong was the exhaust motor for 2nd floor heat was pulling high amps but working for now
Preformed maintenance on a ICP heat pump on the third floor, and a carrier heat pump for 1st and 2nd floor. Tightened wires, took amp draw on back up heat, checked coils, checked defrost cycle, checked zone board and damper motors for 1st and 2nd floor, also checked refrigerant in both. Both are running like supposed to be.
Preformed maintenance on a Amana gas furnace. Tightened wires cleaned flame rod and cleared pressure switch checked all safeties. Has zone board checked zone board and damper motors all preforming in manufacturers specifications.
Preformed maintenance on a Amana gas package unit. Tightened wires, checked safeties and cleared pressure switch checked flame rod and igniter all running in manufacturers specifications.
Checked a Carrier gas furnace and replaced the furnace control board. Also replaced thermostat with Honeywell T-4.
Serviced Trane heat pump system.
Inspected Goodman heat pump.
Preformed maintenance on 2 Lennox heat pumps. Tightened wires took amp draw on electric back up heat all good. Checked UV lights and media filters changed small filters in system did not change UV lights or media filter they did not need to be changed currently home owner has the filters and UV lights to change in the spring when we do AC tune up. Checked both evaporator coils all good no signs of leaks.
Preformed maintenance on a 2010 Goodman 96% gas furnace. Checked safeties and pressure switches tightened wires took amp draw on system. Checked flame rod and igniter, cleared drain on the furnace side of it it is running in manufacturers specifications.
Preformed maintenance on a 2014 Amana gas furnace. Tightened wires, checked pressure switch and safeties, took amp draw on system. Checked duct work did not see any rips or tears in it. It’s running in manufacturers specifications.
Preformed maintenance on 2 Goodman furnaces from 2005. Checked safeties and pressure switches, cleared drain on condensing gas furnace in crawl space, cleaned flame rod. Checked duct work it’s R-6 and it’s sealed. Home owner mentioned that when the first floor comes on he starts to sneeze checked duct work for tips or holes in it also checked plenums it all was good, told him if it really becomes a issue to call Mad Hatter to get ducts cleaned.
Preformed maintenance on a 2010 Trane duel fuel Trane package unit. Tightened wires took amps, checked evaporator coil it was clean. Then checked the furnace side of it and cleared pressure switch, checked safeties, checked flame rod and hot surface igniter all working in manufacturers specifications.
Preformed maintenance on a Lennox has furnace. Checked safeties cleared pressure switch was partially clogged. Tightened wires checked zone board and made sure wires were tight and the system was running in manufacturers specifications.
Preformed maintenance on 2 gas furnaces. Cleared drain, tightened wires, checked safeties and pressure switches. Both preforming in manufacturers specifications.
Preformed Maintenance on a 2011 Amana gas package unit. Tightened wires, checked safeties, checked pressure switch, it is running in manufacturers specifications.