franks the best
Fred knew exactly what was wrong with our AC unit. Had it fixed in 5 minutes.
Glue coming in to furnace was leaking water replaced fitting and operating properly at this time.
Cleared water out of inducer, cleaned drain, ok at this time
Replaced ignitor, ok at this time.
Pressure switch stuck closed replaced and checked operation.
Upstairs furnace gas valve not opening, receiving 24 v, will order valve. Downstairs furnace transformer had failed, replaced, ok at this time.
Removed and replaced cap 50/5 under 10/10. Customer wants paper invoice recommended maintenance annually customer wants to think about it
2.5 ton system completely installed including replacement of the shroud and new disconnect
Includes pad, pump ups, lineset, lineset cover, drain materials, and all miscellaneous materials and labor to completely install.
Arrived and found gas valve failed due to not sensing thermocouple. Pilot will lite but not stay lit. Due to cost of repairs, age and condition it may be time to hunk about a more efficient system.
Performed annual maintenance on furnaces.
Replaced thermocouple in trailer furnace inspected heat exchanger and checked system operation.
Arrived and found system gas line full of air. Purged line. System is operating properly at this time.
Performed warranty check on furnace and air conditioner.