Performed Platinum Comfort Club Membership Tune-Up on Cooling System: checked capacitor, checked contactor. tested defrost operation. cleaned out service panel of bug and cobwebs. checked refrigerant levels. all checks good.
Service Call Fee: no furnace operation, voltage was correct at board, but thermostat was not closing terminals. replaced with AA8444 and tested operation
Yearly Maintenance Check Performed by Travis W.
Removed and replaced capacitor. Installed Aprilaire 8476 Digital Programmable Thermostat w/ Event-Based Air Cleaning. Work performed by John B.
Arrived and found system slightly low on refrigerant, tightened leaking schrader valve on suction line. Charged 1lb of 410a. System is operating properly at this time. Lock out caps would be recommended.
Bad hot surface igniter. Honeywell glow fly replacement.