Service Call After Hours Fee R22 14 years old Unit has a bad condenser fan motor. Attached quote for replacement. I am recording to replace air conditioning due to the refrigerant r22 in it and low efficiency and age. 208-230 PH 1 HP 1/4 RPM 850 Customer had a new furnace replaced. They are food to talk about either replaced motor or just replace the whole air conditioning system.
Performed Platinum Comfort Club Membership Tune-Up on Cooling System: checked capacitor, checked contactor. tested defrost operation. cleaned out service panel of bug and cobwebs. checked refrigerant levels. all checks good.
Service Call Fee: no furnace operation, voltage was correct at board, but thermostat was not closing terminals. replaced with AA8444 and tested operation
Yearly Maintenance Check Performed by Travis W.
Removed and replaced capacitor. Installed Aprilaire 8476 Digital Programmable Thermostat w/ Event-Based Air Cleaning. Work performed by John B.
Arrived and found system slightly low on refrigerant, tightened leaking schrader valve on suction line. Charged 1lb of 410a. System is operating properly at this time. Lock out caps would be recommended.
Bad hot surface igniter. Honeywell glow fly replacement.