On time. Identified problem. Ordered part. Again on time. Installed part. Tested system. Verified I was happy. All while making sure he made/left NO mess! Loved my experience and recommend them anytime.
He was wonderful. He found the problem and fixed it quickly
Good job. Would recommend him
Good so far.
Greg was outstanding. Very professional and efficient. He was very punctual and arrived at the promised time.
Very neat and respectful of my house did a great job. Would recommend there service to everyone
If you accept the proposal in March, you can take 10% off the air duct cleaning.
Arrived and found both systems low on refrigerant. Suspected leak at evap coils. Customer has had refrigerant added to systems for a number of consecutive years. Would need to perform leak search to confirm location of leak. Both systems are 8 yrs old. Due to age, condition and cost of repairs it may be time to think about more efficient systems.
Adapt to electric , & Lineset , pad to fit the heat pump.
Found ignitor had failed replace and upgraded thermostat in back side of home system operating properly and signed 2system Monthy platinum membership
Includes all miscellaneous materials and labor to completely install.
Call back on tech 3/12 found power off and gas shut off from tech called to check making sure we didnâ€™t lock out system but ended up being a mistake checked AC to make sure everything was working properly with that as well found capacitor readings failing. Replaced capacitor and AC operating properly at this time as well as the furnace
Ac repairs, added filter drier, pulled vacuum, added contactor, weighed in factory charge, ok at this time.
Customer is going to need new filter.. did not have available during time of service. Need to get price and availability for gas valve and throttle valve carrier mod. Furnace.
Checked and cleaned furnace and ac system is around 25 years old customer knows itâ€™s age and is interested in future replacement of furnace, a/c and possibly hot water tank
Replaced piece gas line bring to code. Customer also has gas fire place found gas leaking but couldnâ€™t pin point location. Told customer we do not work on home fireplaces but shut off gas near hot water tank supplying gas to fire place and leak had stopped.
Replaced humidifier water line, ok at this time.
Evaluation of furnace found lack of return upstairs. Looking to add full system in attic and add steam humidifier to downstairs furnace
Replaced surge protector on outdoor condesor unit that had failed. Operating properly at this time.
Drain lines clogged cleared system heating properly at this time.
Unit going off on high limit, checked coils, blower motor and wheel, and flue, no issues found. Also verified gas pressure is at correct setting, and performed combustion analysis, no issues found to cause limit switch to open at this time. Will order limit switch and re evaluate.