Very impressed he was very informative and did a great job
Performed platinum cooling/heating check. Adjusted gas pressure from 2.41 to 3.4. Temp rise is good. System is operating properly at this time. Changed customer supplied humidifier panel. Water line temp dehumidifier looks to have been leaking but seems ok at this time.
Nobodyâ€™s home. Miscommunication with office on time of availability
Arrived and found no immediate issues. Seems as though lines may had had air in lines. This was first start up of furnace of the year when issue occurred. This is an older Payne unit. Seems to have little to no maintenance. It may be time to think about a more efficient system due to age and condition.
Performed standard tune up on furnace.
Arrived and found thermocouple, pilot lite and gas valve I poor condition on a 30+ year old natural draft furnace. Repairs would be costly for a syst m of this age not to mention the safety concerns nvolved. His system does run off well head gas.
Performed annual maintenance on air conditioner.
Arrived and found common wire not plugged to contactor terminal. Fitting was only set beside terminal and making intermittent contact, arking and not allowing compressor to run properly. Also noticed that water line to humidifier is not getting water through it. Will need to bring some new humidifier line and shut-off valve to replace upon maintenance.
Plumbing Service- Water pressure repair
Plumbing Service- Replace Shutoff
Install new furnace, ac and coil. New pad (level ground and add pea gravel). New disconnect and line set. Modify sheet metal, gas (up to 20â€™ gas line and fittings) and electric as needed. Run 2 new electrical circuits. New thermostat. New condensate pump (insulate pump and drain line). Cut duct into trunk and position directly at condensate pump. Ed Isaly 304.834.7444 cell
5 mfd run capacitor on carrier infinity. Checked system function and operation. No other issues with system