Did a very good of cleaning my unit.I'm so glad I got those of our house.Very satisfied with my units and the service I recieved
Very impressed he was very informative and did a great job
Whole House Surge Protector
Service Call Fee: No issue found with mini split. Pressures look good. System is operating properly at this time.
Performed maintenance and replaced condenser fan motor.
Install new furnace and air cleaner. Modify drop. Reconnect gas, drain, electric and vent. Need LP kit
Performed annual maintenance on furnace.
Arrived and found both line wires to humidifier canisters burned and melted. Need to order and replace wires. If this doesnâ€™t work then we will need to install two new AA800 humidifiers. Need to perform maintenance once we return for repairs. Installed new humidifier canisters and wire leads. Checked humidifiers while running and draining. Checked furnaces and cleaned condenser coils. Systems are operating properly at this time.
Performed annual maintenance on equipment.
Includes all miscellaneous materials and labor to completely install. We will adapt to the existing duct system, gas line, high/low voltage wiring being used by existing system. We will check temperature rise and upsize 8â€ return with 12â€ if needed.
Preformed warranty check on both mini split systems.
Performed platinum cooling/heating check on 2 systems. 20x25x1 filter for both systems. System is operating properly at this time.
Preformed heating and cooling check.
Arrived and found white aux wire not wired and system is flat on R22 refrigerant. Immediately found primary leak at a hissing discharge schrader core. Need to replace cores and recharge system with 5lbs of r22 to get system operational.