Did a very good of cleaning my unit.I'm so glad I got those of our house.Very satisfied with my units and the service I recieved
Very impressed he was very informative and did a great job
Install new furnace and air cleaner. Modify drop. Reconnect gas, drain, electric and vent. Need LP kit
Performed annual maintenance on furnace.
Arrived and found both line wires to humidifier canisters burned and melted. Need to order and replace wires. If this doesnâ€™t work then we will need to install two new AA800 humidifiers. Need to perform maintenance once we return for repairs. Installed new humidifier canisters and wire leads. Checked humidifiers while running and draining. Checked furnaces and cleaned condenser coils. Systems are operating properly at this time.
Performed annual maintenance on equipment.
Includes all miscellaneous materials and labor to completely install. We will adapt to the existing duct system, gas line, high/low voltage wiring being used by existing system. We will check temperature rise and upsize 8â€ return with 12â€ if needed.
Preformed warranty check on both mini split systems.
Performed platinum cooling/heating check on 2 systems. 20x25x1 filter for both systems. System is operating properly at this time.
Preformed heating and cooling check.
Arrived and found white aux wire not wired and system is flat on R22 refrigerant. Immediately found primary leak at a hissing discharge schrader core. Need to replace cores and recharge system with 5lbs of r22 to get system operational.
Performed platinum cooling/heating check. Adjusted gas pressure from 2.41 to 3.4. Temp rise is good. System is operating properly at this time. Changed customer supplied humidifier panel. Water line temp dehumidifier looks to have been leaking but seems ok at this time.
Nobodyâ€™s home. Miscommunication with office on time of availability
Arrived and found no immediate issues. Seems as though lines may had had air in lines. This was first start up of furnace of the year when issue occurred. This is an older Payne unit. Seems to have little to no maintenance. It may be time to think about a more efficient system due to age and condition.