Excellent job correcting my DIY attempt. Likely their amusing job of the day.
Very knowledgeable and professional, completed the task in great time
Grogg's HVAC Tech Lee was courteous and informative while diagnosing our furnace issue. He was patient as he explained the problems we were having with our furnace and the options for repair. Grogg's has an excellent employee in this young man for both his professionalism and diagnostic service while on site.
Windows were expertly installed, greatly improved sound transfer from outside & enhanced esthetic value of the home
Mr. Scott came to my residence and gave me an estimate on the replacement of my sewer line. He was very knowledgeable and professional at all times. It was a pleasure to work with him.
Furnace stopped working. Service agent deduced what was wrong quickly. Made decision to replace HVAC unit.
I am curious why Travis wore mask and other person did not.
Technician was very polite and professional. We are always pleased with Grogg’s.
Installation of new 60,000 BTU, 96% Efficient, 2-Stage Variable Speed Furnace and 2.5T AC
heating and cooling check
Service Call Platinum Client- water is leaking from evaporator coil drain pans for both units. They are both heavily rusted due to age (1994). Unit on the back right side was low on refrigerant, added 2 lbs of r22 to the system to get correct levels. The system still leaking water. Evaporator coil and pans would need to be replaced to eliminate water leaks. I strongly advise against repair due to cost and age of equipment. The customer is going on vacation and will decide on getting an estimate for replacement after they return
Service Call Platinum Client Arrived to find compressor not starting found failed capacitor that caused the wire to the compressor to burn up. After replacing the capacitor checked the amp draw of the unit. The compressor was within spec but the fan motor was pulling high amps. A system is an R22 unit. I checked refrigerant levels and they appeared to be operating within spec. Discussed considering a replacement in the future.