Always a sense of security and trust with Hobaica technicians
We were very impressed with the immediate response and installation of our new HVAC system. As alway, the staff was on time, friendly and knowledgeable from the time of purchase to the completed installation. Our units were installed in one day. We particularly appreciated the care and cleanliness during the process.
Timely, knowledgeable, professional, personable, and inexpensive for services provided. Can nott get any better than that!
Tom is really a hard worker! He was honest, knowledgeable and very helpful. I will definitely use him again in the future.
Home Inspection HVAC Includes 1 system (12-4 arrival time) $177.45 ***ADDED CC TO PAY SIMPLE*** 30 MIN LEAD TIME TO MEET ON SITE REALTOR TIM
1952 new customer special ac cooling tune up
Return to install hallway toilet, HVAC spring summer maintenance check up for ADI Keri handler and outdoor condenser he fucked
Gratis Compressor (8AM arrival time) Includes: gratis compressor authorized by Rheem, refrigerant recovery, torch for welding, misc copper & fittings, suction drier, vacuum pump usage and about 10LBS R410A refrigerant
WHOLE HOME COMPLIMENTARY PLUMBING INSPECTION (12-4 arrival time)
Warranty 1st Year (12-4 arrival time) From Jacey: "I found there is no low voltage power at the condenser. Upon further diagnosis I found the thermostat wire is damaged somewhere between the air handler and condenser. We will return and run a new thermostat wire." 18-8 or 18-6 TSTAT wire about 20-30 FT
Installed 3 GFCI 1 laundry room, 1 in kitchen amen 1 outdoor.
Unitary inverter gas furnace
Heating split heat pump maintenance attic and ground system set up for winter reading properly now
Review for Amer
Performed a camp maintenance inspection on 2 Carrier split heat pumps located above the drop ceiling and on the roof. Checked thermostat operation, and replaced the air filters. Checked motors, amp draws, run caps, electrical connections, coils, condensate drains, refrigerant pressures, and temp splits. The systems are operating properly at this time. Thank you for choosing Hobaica Services.
Inspected unit in heating Checked temperature difference between supply and return, static pressures, visual inspection for refrigerant leaks, checked motor bearings, capacitors, contactor, amps, flushed condensate line, cleaned condenser coil. Would recommend replacing the system soon due to age and condition of unit
Performed maintenance on splits system. Checked: filter, compressor amp, outdoor motor amp, indoor blower motor amps, capacitors, indoor and outdoor coils, refrigerant pressures in cooling, clean, tightened all electrical connections. Washed outdoor coil with water. The unit is working properly at this point. Thank you for choosing Hobaica Services