Binh is always prompt, polite, and friendly. He is a pleasure to work with and keeps my equipment running smoothly.
I was very pleased to see Bing again. I have complete confidence in his expertise and recommendations.
Michael, who is not our routine PM Technician, did our service today and he was awesome! Not only talented but quite personable! We enjoyed meeting him and we hope to see him again in the future! Well done!
Angel and Ivan were great, showed up right on time and worked hard through the day to get the job done. We were very happy with their professionalism and courtesy.
Your service agent, Danny, was very courteous, knowledgeable, and friendly. He explained everything he was going to check. At the end He explained a possible repair that I consider getting done. He represents your company very welL
Thomas is very professional and personable, he is knowledgeable, he listens well, explains what he’s doing and why, and he’s extremely courteous and respectful of my property. Thank you.
Always a sense of security and trust with Hobaica technicians
We were very impressed with the immediate response and installation of our new HVAC system. As alway, the staff was on time, friendly and knowledgeable from the time of purchase to the completed installation. Our units were installed in one day. We particularly appreciated the care and cleanliness during the process.
South bedroom system, Daikin serial number 2007045094. I found the thermostat reading communication error and system not functioning. I found the correct system in the attic with a bypassed blower limit switch and I verified the limit switch was failed and open. I replaced it with the OEM blower limit switch and verified the condensate safety is dry, then upon resetting outdoor equipment everything came back online operating properly.
Wine cellar repair
Warranty first year
Clear out drain line
Clear condensate drain line.
Perform Quality Control Inspection on 1 system (8-12) 2 YEAR INSPECTION AFTER INSTALLATION
Unit SILVER MONTHLY TCC HVAC TUNE-UP (8-12)
In chandler Az, I completed a scheduled maintenance inspection for 2 split heat pump units. I inspected indoor temperature split, indoor airflow, indoor motor amp draw‘s, flushed drain pans and drain line, changed air filters, checked refrigerant charge, checked outdoor motors and capacitors. The Lennox condenser’s outdoor fan motor is right at its max amp draw of .50 A. This isn’t a huge concern yet but we will monitor the condition of this motor on next visit. Thank you!
Perform bi annual service
In chandler Az. I completed an HVAC tune up on a Lennox split furnace system. I inspected the cooling functions today. I checked indoor temperatures and air flow, checked amp draw and inspected fan motors, flushed drain pan and drain line, checked refrigerant charge, capacitor and tightened electrical connections. This unit is operating properly at this time. No further action is needed. A faulty thermostat was found and replaced under warranty. A Honeywell T6.
In Chandler Arizona, I completed a scheduled heating maintenance on a Rheem split heat pump. I checked temperatures airflow amp draws of motors cleared and flushed drain pan and drain lines, checked capacitors, inspected coils and motors. Checked refrigerant charge. The out door fan motor was found to be drawing excessive amp at 1.15a of a max load of 1.0a. this motor has been over amping for a few inspections. We have just continued to monitor the motor. The unit is functioning at this time.
East AH Indoor Coil Warranty Replacement & East Condenser Sure Switch Compressor Contactor