Binn is very professional, efficient and explains in detail work needed when applicable.
Ethan is a great worker and he kept us in the loop all day long.
Binh is very nice, neat and informative.
Binh is top notch.
Stated the reason he was here and which AC he was to service.
Binh T. was professional and provided excellent service for us when our upstairs AC unit was not working properly! He took the time to explain what the problem was and helped with our options. We’ve always been impressed with the employees from Hobaica and Binh was no different from our previous experiences with this business. Thank you!
Good product and good people
Jorge and Jason were so polite and respectful during the time they were here installing a new air conditioner. They answered all my questions. They worked in the rain and cleaned up after themselves. As they said, “We want to leave your house looking like we were never here.” And that they did. GREAT JOB guys!!!
Gio did a great job. Installed large equipment by himself with no partner. I don't know how he did it, but he did with a smile and great attitude.
In Mesa Arizona, on a customer courtesy car to secure an electrical disconnect box and reattach some sheet metal framing that went around the base of her unit. Also lifted and secured the drain line as it was drooping not allowing for proper drainage. The unit is operating properly at this time thank you for choosing Hobaica!
In Mesa Arizona performing a $49 cooling inspection on a Lennox split furnace and straight cool unit in cooling mode. I recorded and our temperatures, Indoor motor amp draw, inspect indoor coil, inspect drain pan and drain line. At condenser checked refrigerant pressures, compressor amp draw, outdoor fan motor amp draw, inspect outdoor coil, checked and tightened all electrical connections. This unit is operating properly at this time, i got Bruce a roofer to contact
In Gilbert Az, performing a scheduled maintenance on a Lennox split furnace and straight cool unit. Inspected indoor temperature differential, indoor airflow, amp drive indoor motors, inspected motors and indoor coil, tightened electrical connections. At condenser checked refrigerant pressures, checked amp draw of compressor and outdoor fan motor, this unit has inverter technology and has no capacitors, this unit is operating properly and efficiently at this time. Thank you!
Split furnace system York
In Scottsdale Arizona performing a $69 HVAC inspection on a Bryant split heat pump in cooling today. I inspected thermostat function, temperatures across the coil, amp draw of indoor motors. Inspected indoor coil, drain pan and drain line. Checked refrigerant pressures, outdoor motor amp draws, and tested capacitors l, found the dual run capacitor at the condenser weakened far outside of manufacture specs, with approval a TURBO200x 70/5mfd was purchased and installed today. Thank you!
Wine cellar repair
2 split Lennox heat pumps
Maintenance 2 systems and water heater flush
$69 Service Special Fee (8-12) Customer looking for 1 unit maintenance