Phong was great.
Chris is very nice, helpful, knowledgeable, inspires trust. I'm very happy with his service. He left me with a very favorable opinion of Huft Heating and Air. Thank you.
Matt arrived on time and conducted a thorough inspection of my unit in the attic to determine the cause of the malfunction in my Lennox system. His clear explanation of the problem was made easier by the photos he thoughtfully took of the issue. The solution he proposed was much less expensive than I thought it was going to be. Huft installed my system a few years ago and has provided excellent, twice-yearly service--and this recent experience with Matt was no exception. I continue to be a loyal customer.
Outstanding service. Came on time, respected my home (put on booties), offered to clean up a small amount of dust left by repair, clear communication. Could not ask fire more.
Shun showed up on time and was very professional and efficient. Wasted no time checking on the unit in the back then going up into the attic and putting together a quote and going over it with me, answering all my questions.
polite, well informed, told me what was happening, explained charges well
My experience with Huff Heating and Air was outstanding. They arrived on time and got the job done. I would highly recommend them to my family and friends. Their very professional business and answered all my questions with my new unit. Outstanding business
Performed Heating maintenance on a Coleman Heatpump. Replaced new filter, washed outdoor coil, check refrigerant level in cooling mode due to higher outdoor temperature. All checks are within manufacturers spec and system is operating properly.
Preformed furnace tuneup on two Lennox system no issues or concerns at this both systems are operational at this time I talked to client about Iwave and new club membership Client wants to talk it over with his wife before he decides anything
Upon arrival homeowner stated that heater was not blowing any hot air. Upon diagnosis found gas valve switch was tripped are not allowing any gas to feed burner. Reset gas valve and system came on. Ran system for 20 minutes checking temperatures. System is operational at this time.
Performed heat maintenance. Filter is ok, heat rise is within specs. Amp draw on inducer and blower motor is ok. Cleaned flame sensor and burners, flushed drain line. Heater is operational at this time. Signed up on superhero club.
Balanced charge. Removed 8oz r410a to bring subcool to factory specs @ 7Â°. Temp split 21Â°. System is operational.
Found bad pilot assembly. Part is under warranty. Part will be shipped directly to homeowner. They will call us to reschedule when part comes in.
Heating inspection service one heating inspection service removed and queen queen center adjusted gas pressure to 3.5 inches of water column system is operating properly
Performed heat maintenance. All components within specs. System is operational and heating at this time. Homeowner wants to upgrade to guardian club next year to add plumbing and get a free blower cleaning
Installing new Rheem Two Stage Heat Pump System.
Signed up sidekick club. Performed both heat and a/c tune ups today. Checked and cleaned all components. Drain is draining at this time. Replaced filters. Systems are operational at this time. Recommend looking into system replacement due to age, operating condition/cost of future repairs, efficiency and r-22 phaseout. Sign up on sidekick club and perform heat and a/c tune ups today.
Performed heating tuneup for day and night split system. Checked all safeties and connections. Changed Merv 16 filter. System is operational at this time.
Performed Heating tune up on a Ruud furnace. Cleaned flame sensor, vacuumed blower compartment, cleared drain lines, Gas line are leak free, Gas pressure are within spec, Heat exchanger are intact, electrical wires and components are within spec, blower wheel starting to have dust build up; clemical cleaning is advised, and duct work were all secured and intact. System was without surge protection or any air purifier; give estimate for surge protection and I-wave purification. All checks are within manufacturers spec and system is operating properly.
Performed heat maintenance. Heat rise is within specs. Filter is clean, amp draws on inducer and blower motor is ok, cleaned flame sensor and burner. Heater is operational at this time.
Install new timer switch for whole house fan and test. Install new dormer vents on roof to provide better airflow. Seal off dormer vents to prevent leaks. One year labor warranty.
Preformed furnace tuneup on a Lennox system. system has no air Purifier and no flood prevention switch no other issues or concerns system is operational