Chuc was awesome. He was informative fast and friendly five 🌟
Jet was very knowledgeable and helpful. I would recommend him to anyone that needs service.
Not happy with the 17,000 HVAC unit I had installed on May 1st and May 8th still not cooling properly Tech came out, May 11th still not cooling Tech came out replaced thermostat, May 24th system shut down with a cooling problem for 4 hours, tech came out May 25th still not cooling properly. Tech needs supervisor to come out and look at unit better be tomorrow, May 26th
We were super impressed!! Larry did an amazing job and was very upbeat and friendly!!
I love the professional service and quality products!
Always very professional and polite.
I absolutely recommend Huft. And my technician Jet is one of the most friendly service workers ever. If you are looking for a company that will tell you the truth and try to save you money, this is the place to give your business. They communicate via texts, emails, internet chat, phone, and even have people working after hours. As a full time working mom, I really appreciated the different ways and times available to communicate. And if its important to you: they also wear foot coverings, gloves, masks and were very tidy.
Very polite and knowledgeable.
Performed AC inspection and tune up on Lennox split system. Customer provided replacement filter. Cleaned outdoor condenser coil. System is operating properly at this time.
Upon arrival homeowner stated the unit makes a loud noise but recently stopped. Checked the system out and found the unit low on R410a. Recommend doing a leak search. I do not have any dye on my truck. Homeowner would like the unit charged and the dye all put in at the same time.
Performed air conditioning tuneup on Trane condenser. Found system to be operating properly according to manufacturer specifications. Cleaned outdoor coil. Installed hardstart kit. System is operational at this time.
Checked system drain line system is draining properly at this time condensation drip did not come out as fast as client thought it should she thought something was wrong I explain that we just installed Friday system needed time to build up condensation
Performed AC tune up on an American Standard Split System. Upon arrival, customer stated lines were icing up the day before then change filter then ran fine. Found secondary pan was full of water, primary lines were clogged up. Cleared both lines with nitrogen. Evaporator coil was okay at this time. Highly recommend to change filter regularly. System is currently operational at this time.
Found system running but water draining inside on bedroom head. Alex came out and we found that clip holding on condensate hose had broke. Reattached and tried to make it go straight out wall. Ran for about 20 minutes but saw no condensate water. Asked customer to run it normal and call us if issue persists. May need to take unit off wall.
Upon arrival found carrier ac system not working. Found the unit to be 5 pounds low on R410a. Added R410a and a leak search. We will be back in 2 weeks to perform the leak search
Preformed Diag. On a Rheem system I found a bad Transformer I replaced under warranty I added surge protection (bogo) and renewed client club membership
Performed sidekick club maintenance for Rheem package system. Tested and checked system in heating and cooling mode. Checked all safetyâ€™s and connections. Washed filter. System is operational at this time. Signed up for sidekick club membership.
Performed annual AC inspection and tune up on Lennox split system. Cleaned outdoor condenser coil. System is operating properly at this time. Customer concerned that the system is not cooling properly. She will call us if it still feels like the system is not cooling properly.
Found bad dual capacitor on compressor and weak capacitor on blower motor. Replaced both capacitor.
Quoted new Lennox High Efficiency system. Getting back to me at the end of the week.
Preformed ac tuneup on a Lennox system unit has no hard start kit no other issues or concerns at this time system is operational
Upon arrival installed a new evaporator coil. Pump down the system and tested. Low side was pumping down and high side was raising. Pump Dow system again. Left to go get a new TXV and filter dryer. Came back and installed new txv and filter dryer. Tested system. Had 8.5 sub cool and 18 super heat. Temp split is 20 deg. System is operational at this time.
Performed last visit AC tune up on a York Split System. Cleared condensation drain lines, washed condenser coil, all electrical wires and components are within manufacturers spec. Found secondary pan was in rough shape due to rust. System is currently operating at this time. Older system and not as efficient, Would like a comfort advisor for estimate of new options.