Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
Jonathan was very knowledgeable and courteous.
Chris was friendly, efficient and on time. He spent the time to review our systems evaluation and answered all if our questions.
Did not like the way technician criticized me for having a home warranty. It is my peragative. Furthermore, he should not be criticizing other air conditioning companies. It does not look good for Hyde’s.
On time, polite and even gave us a gift card to Starbucks!
Dropped off permit.
I found that the Smoke Detectors are Hard Wired and over 10 Years Old. Recommended replacing Smoke Detectors. Client hears chirping by her Master Bedroom and Master Hall Way. Wants to change just those smoke detectors for now.
Talked with client about flue extension received ok to order
System off upon arrivalâ€” turned system on still not heating Fault code= roll out limit switch openâ€” reset switch and test system now heatingâ€”- Must add flue extension kit ( need to talk with client about flue extension) See note
I Performed Maintenance on all 4 Heating Systems. Also replaced two 20x30 two 20x20 and 16x30 Filters. All 4 Heating Systems are 2013 models located in the attic and on the ground. I also flushed all condensate drains. Everything else checked out fine at the time of service.
Replaced circuit board for bedrooms system serial #CV32AB. Equipment running properly and within limits, also conducted maintenance on 2 heating systems. Washed filters and cleared condensation lines.
I found that the hot surface ignition was no good and I had to go to Cathedral City to pick up a new ignition. I replaced the hot surface ignition and tested and everything is now working at this time
Client rescheduled at door. 2/18. Return to perform service and troubleshoot living room system. Found bad dual capacitor and system extremely low on refrigerant. Opened evaporative coil and found signs of oil in pan. Need new evaporative coil. Performed heat service.
Performed comfort heater service checked burners blower amps and motors replaced filter cleaned drain checked electrical wires and connections
Service heat â€” roof package units Guest bedroom ( mirrored room) has no return filter access grill is NOT removable â€” no impact on coil at this time will monitor
Due to low ambient temperatures there will be a lower temperature split between return and supply air. With low ambient temperatures there is not enough heat in the air to be removed to have a higher temperature split between supply and return air.System is cooling Properly. Removed 30 amp breaker and installed 40 amp breaker for condensing unit.Both primary and secondary condensation lines are clear and draining properly.
Parts for system are obsolete. Barry to follow up
I performed a maintenance on (2) heating systems and I found that the ducting in the attic are deteriorating and I advise client about replacing the ducting. Then I changed out (1) filters and flushed out the condensate drains located in the attic and on the ground
System 1: living: found system with almost no refrigerant. Low pressure 42psi 410a system. System has refrigerant leak. Temperature split of 4Â° System has bad evaporative coil. Also found abundance of water drainage issues. Water in furnace cabinet rusting. under platform and visible organic growth. Repairs would require remediation, evaporative coil replacement, evacuation and vacuum of refrigerant lines, and proper charge replacement. Static pressure high 1â€ and returns using building materials (dead space) for return ducts System 2:bedrooms west: found system operational 1992 Freon unit. Also using building material for returns. System temperature difference 18Â° in cooling. Static pressure with no filter .84. System well beyond life expectancy. Freon unit. Both water heaters beyond life expectancy.
Dropped off warranty book and collected check and signatures