Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
Personable, prompt and efficient work.
Chris was very knowledgeable & friendly. He explained everything very well. I would highly recommend Chris in the future.
Casey did a great job in servicing our A/C systems and gave us good information re: the life left in our equipment and how to plan for the inevitable replacement.
Chris arrived at the beginning of our service window time, immediately diagnosed the problem and was able to fix the problem restoring cool air to our home in less than an hour. Chris did a great job and kept me informed through the service process.
Found unit low on refrigerant 2015 model, added 4 pounds of R-410a refrigerant and tested. Unit cooling properly at this time. Please contact homeowner June 1st to schuelde maintenance.
Maintenance on 2 cooling systems. Packaged units on roof, everything running properly and within limits.
Cust ed on operation of system. 20x30 call to sch maint.
Performed ac service on 1 system. Found unit to be operational but beyond life expectancy.
Maintenance on cooling system. Tested equipment and found everything running properly and within limits, washed condenser coils replaced filter and cleared condensation lines.
Found suction sensor and dome temp harness was eaten by rodent. Was able to get into limp along. Will order on monday
Upon arrival I found the compressor that services air to the common area upstairs is a grounded and shorted. Highly recommending for a replacement of condensing unit and evaporator coil. Please see attached pictures. Please see attached estimates.
Cooling Service 2 Unit Everything Checked out ok
Found thermostat calling for cool but equipment wouldnâ€™t respond. Jumper at thermostat and equipment responded, advised homeowner about bad thermostat and quoted. Replaced thermostat for master bedroom unit with focus 8000 and tested. Unit running properly at this time.
Performed ac service. Cleared condensation lines and condenser coil.
Performed ac service on all 3 systems. Replaced all filters and cleaned condenser coils. Flushed condensation lines from outside. Master bedroom: compressor, condenser fan and capacitor have been change within the last 4 yrs. compressor sound like non condensibles. Bedrooms system: condenser fan motor failing and over all showing signs of ware.
2 systems Cooling Service
Cut primary and secondary lines at furnace to look for obstructions, found lines cleared. Primary line is condensating properly, water leaks to secondary line due to unit not being level properly. Installers to return and level equipment properly.
Cooling Service on 2 System No Issue Everything working fine
Control low voltage wire to packaged unit was exposed and worn out do to age causing a short on equipment. Replaced low voltage wire and also rewired thermostat. Tested equipment after and unit running properly at this time.