Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
Informative, knew his stuff, had great analogies to help this non- techie person understand. Very polite and personable.
Very prompt, friendly and knowledgeable
Extremely knowledgeable and kept me well informed throughout the maintenance service.
Tech arrived on time, went through the inspection process quickly and departed
Hyde’s is the best!
Replaced 3 c/o and 5 smoke detectors
Performed maintenance on (2) heat pumps. All ac/heating and electrical components were working properly. Downstairs unit was o lay wired for cool. Compressors, fan motors were all working properly, cleaned outdoor coils and changed filters. Condensate pump us working properly.
I Performed Maintenance on both of the Heating Systems. Also replaced a 20x20 18x30 and two 14x14 Filters. Both Heating Systems are 2018 models located in the attic. I also flushed both of the condensate drains. Everything else checked out operational at the time of service.
Check heater system clean condensation line and heater burner check sequence of operations found living room system high voltage fuse blow replace fuses tested unit for 15 minutes working ok at this time
Preformed a semi annual heating service on two 2020 Goodman split systems. Furnaces are located in attic, access is located in master bedroom closet. Changed three 16 x 16 and three 20 x 20 filters throughout the house followed sequence of operation checked inducer fan motor blower motor amps Voltage flames and flu pipe. Cleared condensation lines secured electrical connections cleaned out burners and furnace. Checked temperature rise and CO safety switches. Equipment checked out operational at this visit. Signed up on Hydeâ€™s family comfort plan Annual membership Inform client on indoor air purification products
Installed txv under warrenty. Installed grills and remote tstat.
Installed full home ring system with from camera and motion sensors throughout the home.
I found that the run capacitor for the condenser fan motor was no good and it burnt the wire off . I replaced the capacitor and I fixed the wiring and tested
Bad pressure switch customer will, wait till next year
Performed precision maintenance tune up on heating and cooling sides of single gas upflow split system (FAU in upstairs closet). Zero carbon monoxide detected. Changed 14x25 filter. Pvc is sealed and condensation pump is working. Airflow was good. Cleaned out heat exchanger. Cleaned outdoor coil of debris. System needed One pound of r22 Freon addded and unit is at proper temperatures and pressures with and indoor temperature split of 20, compressor, fan motor, and capacitor were all working properly. Insulated outdoor copper lineset with armaflex.
Installed 2 accuclean and bipolar
I Performed Maintenance on the Heating System. Also replaced a 20x24 filter. The system is a 2008 Package Unit located on the roof. Everything else checked out operational at the time of service.
Educated customer on thermostat usage, temperature was not dropping below 74 on set schedule, found that customer had a set hold on the thermostat advise customer that permanent hold will always keep it at a specific desired temp.
I performed a maintenance on (2) heating systems and I found that everything checked out ok. Then I changed out (2) filters and I flushed out the condensation drain located on the ground
Had to install five emergency light replacement fixtures. And also had to check the plugs throughout the property and reinstall some plugs that were taken off . All right