Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
Nice and personable. Helpful and caring
Did his job well
Maurice was very professional and helped us out and explained what a compressor savor would do and how it would benefit our unit.
Thor called before his arrival. He checked things out and concluded there was a problem with a Freon leak. He fixed it and that was that.
Maintenance and safety check on air-conditioning â€”â€”system is microchannel package unit â€”â€”see photo for model and serial numberâ€”- unit is cooling for manufacturers recommendations reference 19Â° air split â€”â€”-outdoor coil super super dirty removed protective louvers and clean system had a faulty dual run capacitor reference 70/10 was 69/8 replace capacitor
Preformed a semi annual cooling service on two cooling systems 15+ model and 2011 American standard, both split systems. Cleared condensation lines and changed two 20x25 filters located within the furnace/ garage and outdoor closet upflows. 3.5 ton condenser is located on rooftop and 3 ton condenser is located on ground. Cycled equipment check capacitor, fan motor, compressor, hard start, Amps and voltage. Secured and clean electrical connections and condenser and fuse box. Checked refrigerant so cool, superheat and line temperature. Thermostat checked out OK. Rinsed condenser coil. Upon arrival found found Bryant condenser not operating, within further inspection found run capacitor to be at 0.00mf informed client on findings Highly recommended system replacement due to age and refrigerant, Office will contact client for replacement operations. Inop. American standard/ recommend and replaced 2 weak capacitors, 15 and 30uF. American standard system is now operating efficiently and
Deliver warranty book and replaced 20x30 filter.
Replaced 3 GFCI 1 under warranty
Service both system 2012:system see previous ticket
Living room low 2pounds advice and added service both system bedroom system low between 3 to 4 pounds also replace capacitor for bedroom system per customer sent estimate
Upon arrival client turn system on to cool but only blower motor and compressor would operate. With further inspection I discovered system had a faulty capacitor. Installed new 40/5 ÂµF capacitor and cycled system. System now operating properly. Client stated he has 10 years parts and labor warranty.
Unit working on arrival. Checked voltage and amps are within range. Possibly over heated compressor.
Bad dual capacitor.replaced and tested.
Found bad condenser fan motor. Replaced and tested. Client had breakers tripping too. Wants electrician to come out tomorrow of at least sch someone.
Replaced txv and filter drier. Pulled vacuumed to 500 microns. Unit is now cooling properly.
Added to get by
Low voltage short. Replaced tstat wire to condenser. Unit is now operating. Recommend maintenance on equipment.
Performed cooling maintenance on 2015 Lenix split system. Changed out 20 x 25 x 1 and 20 x 30 x 1 filter located in ground and inside furnace cabinet. Furnace is located inside hallway closet. Checked all electrical components and refrigerant levels, found starting amps out of range recommended and installed compressor saver kit to help compressor at start and prolong life of unit. Starting Amps are now 94/144, checked capacitor checked across contactor. Checked sub cool and superheat and line temp. System is within manufacturers specifications and cooling and operating properly at this time of service cleared condensation line at FAU and washed condensing coil
Bad capacitor in other system. Replaced and tested