Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
Just had my winter annual tune-up by technician James from Hyde's. Prompt, courteous and through. Hyde's program gives me piece of mind and ensures my AC/Heating systems are functioning at their optimum.
Frank Velarde was fantastic! He was very professional, courteous, and provided me with some very helpful information on how to keep my unit in good condition.
We truly feel safe and know Hydes will give us the best service and a great price. Looking forward to many more years with the company.
Casey was a great representative of the company and displayed his knowledge of his profession
Casey is one of the most patient and smartest service person ever.
Performed annual heater maintenance on two 2007 Goodman furnace located inside attic. Changed to 20 x 20 x 1 filters. Checked amps, volts, temperature rise and all safety switches. Checked gas and static pressures also checked capacitors and flushed condensation lines. Found all electrical and safety components to be within manufacture specifications both systems are operating and heating properly at time of service. Recommend installing condensation water safety switch and Jones cleanout valve on both systems to prevent water damage to the home or equipment due to Condensation back up or overflow and Jones clean out valves to ensure proper flushing of condensation lines.
Garage check heater system working properly clear condensation line, It drains in bathroom
Wires issues need to came back tomorrow
I Performed Maintenance on the Heating System. Also replaced a 20x25 filter. The system is a 2011 model located in the garage. I also flushed the condensate drain. Client has Acitvetek UV Light cell that is no good. Advised client that the cell needs replaced and client wants to get it done. Office to call and schedule when part comes in. Everything else checked out operational at the time of service.
Hung two ceiling fans one in the living room one in the bedroom also moved a light had to cut in a new box for the new light And also hung five lights didnâ€™t have a chance to do the switch need to come back to finish the job
Comfort heater service on r22 2006 Amana packaged unit. Replaced filter in upper hallway wall. Checked lol heater components, static pressure, volts, amps, gas pressure, safety switches and capacitors. Found dual fan motor rated for 5uf and reading 3.9uf. Advised client on issue. Found random box on supplies from the original install under the blower motor hidden. Removed items. Found condensation line pvc and not up to code. Water heater is 50 gallon 2003. Advised client on age and type of Freon. Advised client on December special. Mike to follow up with estimate.
Service Heating two times â€”â€”furnaces are located in the attic â€”â€”attic access is off kitchen in the pantry â€”â€”furnaces heating per manufacture specification â€”â€”temperature rise mid range both units â€”â€”clear condensate line from attic 2x
Waiting for a/c pro to all me back for gas valve
Dropped off permit also kitchen System not working on heat after further inspection found bad gas valve waiting for supply house to see if they have and stock
Upon arrival client stated water coming from the return. Found signs of water on the floor and inside return. Checked roof and found water sitting by return where it connects to the roof. Connection in about 6â€ up from roof. Advised water is sitting there and going into the connection. Advised to call hoa about roof issue. Replaced filter. See pictures and videos.
Gave options on American Standard
I Performed Maintenance on the Heating System. Also replaced a 16x30 filter and flushed the condensate drain. The Furnace is a 2002 York model located in the outside closet. Everything else checked out operational at the time of service.
Installed Hot water heater and tested.
Left 8 foot ladder for inspector in living room per homeowners request. Left permit with homeowner and advised about inspection. Made sure unit was up to code and will pass inspection.
Performed furnace maintenance on single American Standard horizontal split system (converted from 2 to 1). Monitored all heating and electrical components and all checked out to manufacturerâ€™s specifications. Cleared out condensate drain and changed 20x24 and 20x20 filters.