Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
Technician very knowledgeable
Chris and Jose were efficient and neat. Long experience at their craft was quite apparent.
Answered our questions. On time and efficiently done.
Jeff was a terrific technician who took the time to listen to questions and answer in a way that I, as someone who is not knowledgeable about heating and air conditioning, could understand. I’d love to have him anytime I schedule service.
I already didd
Client stated thermostat not holding temperature ( since last maintenance visit ) thermostat working at time of arrival recommend replacement client agreed
I Performed Maintenance on both of the Heating Systems. Also replaced two 16x30 and 12x24 Filters. Both Heating Systems are over 10 years old located in the attic. I advised client about replacing the systems and advised about financing. Client has home warranty. Everything else checked out operational at the time of service.
Pick up material
Service two air conditioners located on the roof package unitâ€”â€” Amana Unit had low-voltage wire in need of repair repaired per clients request both air conditioners are cooling per manufacture specification
Preformed a semi annual heating service on 2005 Coleman furnace. Located in laundry room. 3 Ton Condenser is located on ground HCFC 22 Changed out two 16x20 filters located at furnace. Followed sequence of operation and checked capacitor, volts, amp, heating safety switch and heat exchanger. Thermostat checked out ok. Everything checked out operational at this visit
Short in condenser wire. Pulled on wire short went away. Probably touching somewhere under the coach. Told client if it happens again he will have to run new wire.
Performed annual heater maintenance on American standard split heat pump. Air handler located inside garage. Change 20 x 20 x 1 filter located inside air handler. Checked amps, volts and temperature rise. Checked all electrical and refrigerant levels at condensing unit. System is operating and heating properly.
Remove blower wheel and housing to clean install Honeywell UV LIGTH air purifier and tested working properly I also called home owner to advice to leave thermostat an fan on during the day and fan auto during the night for best results
Replaced gfi in m/ bathroom
Performed heater maintenance and safety check on upflow furnace located in closet. Cleaned blower compartment surrounding furnace area. Checked sequence of operation insured wiring is secure and tight. Found blower motor run capacitor week and outside of manufacturer specifications. Client decided to replace blower motor capacitor. Ran system in heating and checked amp draw on blower motor and inducer motor. Replaced 20 x 25 x 1â€ filter. Didnâ€™t notice excessively loud noise coming from outdoor unit and made client aware. OK Nancy all finished up Nancy any questions for me
Performed heater service. Bad blower cap. Replaced 7.5uf Found bad evap coil. Sch replacement of condenser and coil for May 5th
Preformed a semi annual heating service on 10+ Lennox split system. Furnace is located in attic/ laundry room access. Condenser is located on roof/ above garage. Changed 20x25 filter located in ceiling. Followed sequence of operation and checked capacitor, amps, voltage, heating safety switch, temperature rise and water safety switch. Cleared out condensation drain line, safety pan has rust from previous flood. Cleaned out burners, electrical, furnace and platform Thermostat checked out ok. Equipment checked out operational at this visit.
I performed a maintenance on (1) cooling system and I found that the system was (3) pounds low on R-410a Freon and I recharge the system and tested. I also advise client about system having a leak. Then I changed out (1) filters and I flushed out the condensation drain located on the ground
I Performed Maintenance on the Heating System. Also replaced a 20x30 and 14x14 Filters. The Heating System is over 10 years old. I also flushed the condensate drain. Everything else checked out operational at the time of service.
Installed water safety switch on secondary condensation outlet installed 30 amp fuse and removed tape from door switch.