Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
As usual Mike did a good job with the digital thermostats.
Half of our house AC was out and Jeff was prompt about fixing it and gave great service with a smile.
Danny was very good and was very nice and did a great job.
Great guys. Hard workers. 👍👍
Excellent service, friendly and professional
Taylor is so knowledgeable efficient personable and conscientious. All wonderful experience
Returning sat 9-10 WiFi and miscellaneous Service cooling (2) location roof package units (17 years ) informed client units are past life expectancy â€”- refrigerant numbers are within specificationâ€”â€”Sn 2992 recommend dual run capacitor replacement due to age ( capacitor at low end of good)â€”â€”both compressor starting over rated amps recommend start kits ( optional equipment)â€” Sn 9814 blower capacitor out of specification recommend replacement Client interested in WiFi thermostats see estimate Client purchased service plan 06-15-19 Install thermostat Honeywell 8000 (2) with â€œgate wayâ€â€”units connected and test with internet =ok ( client to patch wall as needed ) Client aware of recommendation made on 06-12-19â€” has home warrantyâ€” No work / repair at this time Client interested in ductless for garageâ€”will turn job over to supervisor
See invoice 06-12-19
Replaced living area 950 thermostat with 1050, set up zones the same way living 100% and office 38%. Connected to WiFi and Nexia and deleted old thermostat from his account. Warranty no charge.
Found system low on refrigerant. Will talk to hydes about warranty for coil.
Found compressor over heated cooled off and tested. Recommended comfort plan.
Found system iced at returned Freon good air flow
Check system for noise near return. Client advised itâ€™s not the air noise. Went in attic, removed panel and checked blower wheel. Client keeps 68 degrees and it may be icing causing pressure in blower wheel. Client to advise.
Living area low refrigerant. Made client aware of leaking system. Mostlikly slow leak.
Check system Freon good set schedule to all 82 degrees
Found east unit low on Freon replace o ring in TXV and recharged. Signed up for yearly
System was at 90Â° tripped sensors told client to not go over 85
Reset â€œpresets home away sleep
Installed Honeywell 5000 thermostat and explained operation
Installed a 4 Ton Silver 14 Horizontal Condenser and Evaporator Coil.