Have any feedback for us? We'd love to hear it! Call us at (760) 910-7600 and let us know how we are doing.
Thor was terrific
Great service and technical advice on features and efficiency. Also provided info on a humidifier system when I asked him.
Chris identified the problem quickly and replaced the old, shorting breakers with new ones on the spot. Afterwards the initial problem (non-working fridge electrical outlet) was still not solved. More investigation and the loose wire was detected. Promptly repaired and problem solved. All done with a smile. We received the call ahead making it easy to prepare for Chris' arrival. We called in the morning hoping to get service that day, and indeed we did. All in all very pleased.
Efficient, clear concise explanations.
Service guy was very personable and informative. Explained everything.
All good as expected
Casey’s always on time always informative get in and out quickly.
Been with this company as my maintenance provider for many years. Very happy with the service and the quality. Highly recommend!
Heat pump system on the roof heater system working properly
Check heater system clean condensation line heater components working properly FUA outside closet
Performed heater maintenance on package unit on roof. Changed (2) 14x25 filters and one 16x16 filter. Cleared condensate drain and cleaned inside cabinet to unit. Monitored all heating and electrical components and all checked out to manufacturerâ€™s specifications.
Performed heat and cooling service on a 1 time basis. Ac is low on refrigerant. Client decided to wait for summer to add. Gave client options for replacing cond./coil. Furnace within manufacture specifications. Lowered fan speeds. Recommended replacement. Waterswitch, WiFi stat.
Performed heater service. Both systems within specification. Adjusted airflow. Gave options on humidifire, water switches and tune up elec.
Quote to install 11 white Bar type registers and Bar supply registers and one 20x25 filter return. Need to return to replace 14x8 has a dent in it also install 18x6 after tile is cut
Performed heater maintenance on unit in inside closet. Changed 16x25 filter and cleared condensate line. Cleaned out dust in furnace cabinet. Took CO measurement and got 10 ppm. Monitored all heating and electrical components and all checked out to manufacturerâ€™s specifications.
Performed a semi annual heating service on 2014 Day&Night split system Burners checked out OK Igniters checked out OK Electrical checked out OK Induction fan motors checked out OK Blower fan motor checked out OK Carbon monoxide levels checked out OK Thermostats checked out OK Gas pressure checked out OK Safety switches checked out OK Cleared condensation lines with CO2 Changed 20x25 filters located at furnace/ hallway closet Recommend water safety switch to keep furnace from flooding Equipment checked out operational at this visit
Performed a semi annual heating service on three 2011 American standard split system Burners checked out OK Igniters checked out OK Electrical checked out OK Induction fan motors checked out OK Blower fan motor checked out OK Carbon monoxide levels checked out OK Thermostats checked out OK Gas pressure checked out OK Safety switches checked out OK Cleared condensation lines with CO2 Changed filters through out the house Furnaces are located at outdoor closet Equipment checked out operational at this visit Filters needed 3-10x30. 3-10x10. 5-6x20
Performed a semi annual heating service on 2007 model heat pump Motor checked out OK Compressor checked out OK blower motor checked out OK Capacitor checked out OK Reversing valve checked out OK Homeowner supplied filter 18x18 Equipment is R22 Equipment checked out operational at this visit
Client requested for us to call back in December
Placed new panel schedules
I Performed Maintenance on the Heating System. Also cleaned a washable filter. The system is a 2014 model located in the inside closet. I then flushed the condensate drain. Everything else checked out operational at the time of service.
Inside closet check heater components working properly clean condensation line wash filter
Performed a panel tuneup. Will return November 14 to place the panel schedule