Jose and his brother was very helpful answering all my questions with installation of my air conditioner. Jestin to was helpful with questions i asked.
Found and corrected our AC issue in 30 minutes. Did not try to sell us a new unit. Was honest and a real gentleman. We have a room that never seems to cool enough...had the technician look at it. He knew of a solution. Love this company!!
Integrity is prompt and always gives me a report I can understand on the status of our systems. Their communication is excellent. I get reminder calls, but never feel pressured.
He treated us with the utmost respect. He was speedy and efficient. He seemed to know exactly what was wrong with our unit and promptly fixed it.
Integrity air has been repaiing my old unit for 2 years now and 2 things stand out to me, honesty and professionalism. That is why when I was ready to replace that old unite I called Integrity Air. Justin was great. He took his time to make sure we were happy. They did a great job and gave me a great deal.
Spring cleaning of HCAC. Changed all filters and cleaned units and coils. Nice job
Went right to the issue and discussed options.
Justin and Chris are great!
Preformed cooling tune up blower cap needed to be replaced pan was dry filter was clean checked pressures they were good washed coil checked electrical unit is operating properly
Replace capacitor at condensing unit on a Goodman checked pressure amp draw and all electrical components replaced old cap with new turbo 200x
Installed a new 3 ton 16 seer Amana Unit for a wonderful family here in Mesquite.
Preformed tune up unit is cooling
Preformed tune up
Checked unit had 20 degree split pressures looked good had 15 degree subcooling unit is cooling
Checked 2 units on roof added Freon to down stairs also replaced shrader valve now cooling properly upstairs unit cooling properly did not need to make repairs on it
Added r22 and added new turbo capacitor and blower cap unit is now cooling great need to get quote on new unit
High pressure switch tripped reset washed coils checked pressures and split as well as electrical unit is cooling
Unit low on 410a added free b unit is cooling properly now
Checked water cooled unit temps were off checked cooling tower filter line temps at unit seem to be off looker for a water filter need to return ASAP and check further
Found float switch tripped so I blew drain also recommended they replace thermostat did repairs unit is cooling properly
Locked out stat and set cooling to 72
Installed remote sensors in offices
Preformed cooling tune up added 410a changed filter unit is cooling properly