First time I got photos of what he was doing and what things in the unit look like. I thought that was cool
Kenny was professional and thorough. An asset to Jackson’s!
Work was done efficiently and in a timely manner.
Came on time polite ,& respectful Did the job and and let us know if there was AC my thing Ed lane C we needed to let him know
I wish they would have called prior to coming to my home, but I appreciate them informing me of a potential snake problem with the shake skins they said they saw in the crawl space.
good technician goood service
Tech answered all questions and was very professional
Upon arrival tech found blank thermostat, after further inspection tech found blown 24v fuse due to low pressure switch wires rubbing through. Tech replaced fuse and taped up wires where they will not run through again. No charge per maintenance was just performed not to long ago.
Tech found compressor contactor chattering. Confirmed contactor, defrost board, and blower control board are wired correctly. Found wire rub where high pressure switch wire is shorting on reversing valve coil. Taped up high and low pressure switch wires and reversing valve wires. Still chattering. Tech found coil temp sensor disconnected from defrost board and shorted to cabinet. Plugged back in. Still chattering. Tech disconnected thermostat and tstat wire from unit. Unit ran correctly in each mode without issue. Yellow low voltage circuit is using a black wire from previous low voltage issue. Tech disconnected tstat wire and isolated at both ends. Tech found most of the thermostat wires have continuity together. Tech disconnected common wire at unit and thermostat and installed AA batteries. Tested system with batteries in thermostat. Contactor is no longer chattering. Brown is G for blower. Black is Y for compressor. Tech recommends having 2 techs fish new thermostat wire 25 fe
Tech washed and serviced unit
Tech found no difficulties at this time. Homeowner extended PSA. Tech left homeowner with filter.
Performed CMA Full service on 2 Gas Packages and 8 Split Systems. Gas Package number 1 has a bad inducer draft motor, checked Gas Package 1 burners, burners didn’t come on due to bad inducer draft motor. Recommend replacement of inducer draft motor. Office provide estimate for replacement of inducer draft motors-$1272.94. Split System 4 at Church building Compressor capacitor rated for 70 mfd. Currently using a 50 and 20 mfd capacitor . 20 mfd Capacitor tested at 2.175. Provided estimate of capacitor- $205.28.
Tech preformed CMA INSPECTION on 9 split systems, 1 gas pack, and 1 mini split. All systems are operating correctly at this time. Tech changed all air filters per agreement. Tech has attached system performance reports to invoice along with pics.
Performed CMA full service on 2 rooftop package units. All systems operating correctly at time of service.
Tech found new fan blades broken. Fan blades were hitting suction pipe. Tech will need to return with motor and blade. Unit can only run emergency heat at this time
Tech washed and serviced unit
Could not perform ESA due to inclement weather conditions. We’ll need to reschedule.
Tech found no difficulties at this time. Homeowner didn’t need filters changed so tech left homeowner with filters.
Performed ESA, homeowner extended PSA.
Performed ESA. Technician found no challenges at todays visit. System is operating normally with a delta t of 17 degrees.
DEMO RETURNS & INSTALL NEW CEILING BOXES