Please read my reply from the services performed 🙌🏼
-Performed CMA inspection on 2 split systems. -AH-3: Blower motor belt loose. Unable to tighten further ; suggest replacement of belt. Approximately 41“ in length. Actual part number to be found at office. Provided estimate $205.71. -Recommend more frequent replacement of air filters.
Performed ESA, recommended uv light. Homeowner stated she will call in to get it scheduled. Kenny only.
FOUND PRIMARY FLOAT SWITCH TRIPPED. CLEARED CLOGGED DRAIN LINE. SYSTEM BACK UP AND COOLING. SERVICE WARRANTY.
Performed ESA, recommended uv light.
Tech performed tune up on carrier split system
Tech serviced and cleaned carrier split unit.