Rodney did an excellent job. He seemed to have a good working knowledge of my equipment and performed the service in a timely manner. He was very good at explaining his findings and is an employee you should be proud of .
Annual maintenance on a Trane package heat pump and a Trane split system.
HVAC Commercial Maintenance Sales Call #JacksonAndSons #PreventativeMaintenance #HeatingAndAir
Inspected heat pump.
Sinspscted heat pump.
Inspection on 20 Ton Trane heatpump, LG mini split, make up air, and exhaust fan, changed filters.
Condemned Trane split system. Set up comfort consultant for system replacement.
REPLACING ZONE CONTROL BOARD ON TRANE SYSTEM
Installed auxiliary drain pan with float switch under Air handler.
Installing new aux drain pan under Goodman air handler
Replacing dehumidifier on Carrier split heat pump.
Inspecting Ultra-Aire dehumidifier.
Replacing failed thermostat on TRANE heat pump
PERFORMING TUNE UP ON 2 CARRIER HEAT PUMPS