Replaced blower motor and cleared drain line .
Performed inspection on 3 TRANE units, 2 Dehumidifier, changed all filters. Emptied condensate pump of water, found no power at dehumidifier outlet. Possible bad blower at AH #3 (restrooms). Left case of 20x20x1 filters.
Found coil to gas furnace froze up. Will need to de ice coil to further diagnose Immediately turned heat on and de iced coil Found system low on 410a Homeowner does not want new system at this time. Added 2 pounds 12 oz system is back to cooling properly
Tech preformed CMA FILTER CHANGE. All filters changed.
Tech is servicing two Trane gas packs.
Tech performed routine service