I needed some electrical work done with outlets that weren’t working. Also, had an issue with wiring with a celing fan I installed. i just moved new tenants into the unit and need issue resolved fast. The electrician was awesome, Was very professional, patient and made sure I was satisfied. Needless to say I was extreme satisfied. Just found my new electrical and A/C repair company.
1)â€”â€”Remove 50 amp 4 prong outlet and install new 50 amp 4 prong outlet. 2)â€”â€”Supply and install 50 amp 4 prong range cord.
Replace (1) 125 amps indoor panel Replace (1) broken GFCI outlet in bathroom Diagnosis outlet in kitchen and bathroom, living room not working Troubleshooting range outlet sparking and inspect indoor panel and range outlets Rough patch and clean area Permit fee will be passed through customer if requested
AC not cooling
No issues were found. Freon is good, 61 degree at supply vents
1)â€”â€”Remove 3 125 amp fuse panels. 2)â€”â€”Install 3 new 125 amp main lug 12/24 circuit panels. 3)â€”â€”Label, rough patch and clean area. 4)â€”â€”Run circuit from middle unit panel to exterior wall and install weather proof junction box for new security light. 5)â€”â€”Remove all 9 security lights. 6)â€”â€”Remove porch light from left and right unit and install junction box to extend circuits for new security lights to be installed. 7)â€”â€”Install weather proof junction box in front of left and right unit. 8)â€”â€”Extend circuit from new weather proof junction box in front of left unit to left side of building and install another weather proof junction box. 9)â€”â€”Supply and install 10 double flood LED motion detected security lights. ADDITIONAL; 1)â€”â€”Extend security lighting circuit from Unit 235 B to side of unit. 2)â€”â€”Install weather proof box and double flood LED motion detected security light. 3)â€”â€”Install 7 weather proof boxes for security lights to be i
Detected problem caused frozen coils. Replace existing 12â€ flex duct of the return by 14â€ flex to match with equipment efficiency, approximately 40ft.
Fixed clogged A/C drain line, AC water leak fixed
Fixed A/C drain line which was backing up water into house. Old line was installed incorrectly.
Diagnosis (3) outlets in bedroom not working. Fixing the problem including replace bad outlets or breaker circuit, not including wire being interrupted inside conduit.
Replace 4 tons America Standard AC system. Package unit
1)-----Remove exsitng outdoor 100 amp disconnect and meter enclosure with mast and weather head. 2)-----Install new 200 amp meter enclosure. 3)-----Install new 2 inch rigid mast and bring mast through roof to meet code requirement for service entrance cable height. 4)-----Install new outdoor 150 amp 8/16 circuit main breaker feed thru panel. 5)-----UPDATE GROUNDING SYSTEM: includes the installation of 2 new ground rods, 1 water pipe ground and 1 low voltage ground bridge all interconnected with #4 gauge bare copper feeders. 6)-----Remove indoor 100 amp main lug circuit panel. 7)-----Install new indoor 150 amp main lug 20/40 circuit main lug panel. 8)-----Label, rough patch and clean. 9)-----Run new #1 gauge copper service feeders throughout system. (Approximately 70ft*3=210ft) 10)-----Remove old AC disconnect and replace with new 60 amp nonfuseable pullout disconnect. 11)-----Remove all devices---Switches and outlets. 12)-----Install 13 new tamper resistant outlets with cove
Heater kit replacement 7.2/9.6 kw
Replace 150 amp indoor and outdoor panels