I needed some electrical work done with outlets that weren’t working. Also, had an issue with wiring with a celing fan I installed. i just moved new tenants into the unit and need issue resolved fast. The electrician was awesome, Was very professional, patient and made sure I was satisfied. Needless to say I was extreme satisfied. Just found my new electrical and A/C repair company.
Installed main grounding system, helped install 4 inch for weather head.. Made material list too complete outside Outside wire pulled into panel and into weather head , see pictures.. installed 2 indoor ac mini split units, see pictures.. installed j box underneath meter installed unistrut for porcilin holdster. For serviceâ€¦. Today me n Corey ran new wires and connected the laundry room circuit. Ac needs too be moved over in bedroom and ac lines needs too be ran too back bedroom from outside. All switches and outlets installed except the oven ,I need a special box for thatâ€¦.
Supply and install LED Wrap around fixture in kitchen, Repair post lights not working in front of home. Replace GFCI on outdoor post with new WR outdoor GFCI. Pulled in 6. /3. For range, took down kitchen light installed 4 foot led light for kitchenâ€¦ ran new 12 /2 if wire. Installed new we box, we gfci and bubble cover. See picturesâ€¦ one light not working gotta bow new wire too it. , will be back too finish
Supply and install new outdoor meter and riser. Riser is below required height by code. Re-run a total of (7) circuits to remove old cloth wiring. Reinstall devices and breakers after circuits have been ran. Pull permit and get inspections. Iâ€™m putting a led 4 foot wrap around light in kitchen ceilingâ€¦.. fixed outside post lights. 3 in total.. passed inspection todayâ€¦
Ran inch and a half pvc to meter , knocked out inch and a half into meter 2 times , strapped, took measurements for wire , installed ac disconnectâ€¦
Increase main electrical service to 400-amps, 120 / 240 volts, 1-phase. Remove old electrical meters and main breakers and replace with new. Upgrade tenant main circuit breakers from 60-amps to 125-amps. Reconnect existing laundry room panel. Run new conduit and wire to unit being remodeled to upgrade capacity for new 125-amp panel. Run empty conduit from new electrical service to occupied tenant unit through other unit for future expansion.
Installed boxes and mud rings in the kitchen and living room, installed disconnect switch and wired hot water heater, dug and installed copper ground rounds 6 foot apart for main grounding system.. Corey drilled out hole for ser wire.
Remove old cloth covered wire and replace with new â€œRomexâ€ type cable. Replace old 60-amp electrical panel with new 125-amp panel and new â€œArc-Faultâ€ / GFCI circuit breakers. Supply wiring for new air conditioning system. Supply wiring for new tankless water heater. Update all wiring to new code. Supply and install new smoke detectors to code. Provide all new wiring devices including â€œtamper-proofâ€ receptacles, standard switches and GFCI devices per code. Permits and inspections included. Patching / painting by others.
Check connections coming in from FPL and make sure they are working
Hello Clara! Thank you for choosing Kings Electric and A/c with your electrical needs. Today we had the pleasure of installing a brand new top of the line 100A flush mount electrical panel. The reason for the upgrade was because when first inspected we noticed that the reason you were having issues with certain circuits was because they were burning up. About 4 of your original breakers were already melted and needed to be swapped out immediately. Due to the melting of the breakers your bus bar melted as well which the reason for the whole panel upgrade. We were happy to arrive just in time to avoid an electrical fire. We hope that you enjoy your new upgrade and we look forward to servicing you again! Your Service Electrician Jeahn C Bermudez
Replaced outdoor fan motor and blades . Unit started up and sounds a lot quiet and more efficient.
Hey Melinda! Thank you for calling Kings Electric & A/C for your electrical repairs. Today I was called out because youâ€™re having issues with your 30 amp water heater circuit. I looked at your water heater and the one you purchased was for #6 wire 60 amp and you have a #10 wire on a 30amp. I was able to rewire the circuit to the new wire size, I tested all sinks and shower with your tenant for about 15 mins, and the hot water was working and nothing tripped. If you have any questions or concerns, please reach out. Your electrical technician, Xavier
Hey Melinda! Thank you for calling kings electric & a/c for your electrical upgrades. Today I came back because you were having issues with some outlets. Iâ€™m glad to inform you that everything works once again. Also I gave you an additional quote for the exhaust circuit in the kitchen. If you have any questions or concerns, please reach out. Your electrical technician, Xavier
Hey Melinda! Thank you for calling kings electric & a/c for your electrical upgrades. Iâ€™m glad to inform you that job is complete. The panel was swapped out with a brand new 150 amp main lug panel and everything was tested correctly and everything in the unit turned on. Also the circuit 30 amp circuit for the water heater is there and ready to be hard spliced and I explained it to Charles as well, finally all outlets, switches, GFCI, & smoke detectors were replaced with brand new ones. Thank you for everything once again and if you have any questions or concerns, please reach out. Your electrical technician, Xavier
1)â€”â€”Remove 50 amp 4 prong outlet and install new 50 amp 4 prong outlet. 2)â€”â€”Supply and install 50 amp 4 prong range cord.
Replace (1) 125 amps indoor panel Replace (1) broken GFCI outlet in bathroom Diagnosis outlet in kitchen and bathroom, living room not working Troubleshooting range outlet sparking and inspect indoor panel and range outlets Rough patch and clean area Permit fee will be passed through customer if requested