excellent workmanship and honest, difficult to find in south Florida
knowledgeable and price right
â€” Replace (2) flood lights by Rings security lights, approximately 25ft high from the ground â€” Open supply plenum and seal and mastic from inside
Happy Tuesday Brian! Thank you for trusting in Kings Electric for your electrical needs. Today we had the pleasure of Supplying and installing (2) bathroom exhaust fans with switches in both Master Bath and Guest Bath. In one bathroom we removed a ceiling fan and added a switch leg to the new exhaust fan. In the other bathroom we extended the switch leg from a nearby recessed light. Due to the lack of attic access we still managed to install both exhaust fans fifth no major repairs to the ceiling or drywall. It was a pleasure servicing you today and we look forward to helping you out in the near future. Your Service technician Jeahn Bermudez
Supply and install new pool timer. Replace wiring from pool transformer
Pump is working properly Customer accidentally keeps fan ON
Replace (1) 3A circuit board fuse
Replace (1) GFCI outlet
Supply and install new condensate pump in bedroom AC.
Supply labor and material to clean condenser coil. Flush coil after cleaning. Extend dryer vent away from condenser
Hey Shelly! Thank you for calling kings electric & a/c for your electrical upgrades. Today I was able to remove existing 200 amp main disconnect, and old sub panels as well. Iâ€™m glad to inform you that the job is complete, youâ€™ve upgraded your main disconnect, wiring, breakers, and you added a whole home surge protector as well. If you have any questions or concerns, please give us a call. I hope you have a great weekend! Your electrical technician, Xavier
Recharged unit with 12 lbs of 410A refrigerant. **Note** Possible slow leak could have caused reason for low pressures. Added Refrigerant cannot guarantee complete fix. Identify the leak by electronic leak detector Evacuate Freon and recharge after seal the leak Solder copper to seal the leak which found at the joint between the TXV bulb tube and low pressure line
Remove existing air conditioning duct-work from attic space. Remove old round supply grills in ceiling. Patch & paint by others. Suppl and install new air distribution system in attic using fiberglass and flexible duct system to code. Provide thru-wall return grills where required. Permits, inspections are included.
Remove all existing attic insulation, debris and reinstall new R-38 fiberglass blown insulation.
Office Bathroom- Install Dimmer switch for sink light Install New fan switch Master bathroom- Install 15amp Outlet for small TV Run Coax cable and add Coax jack at location of TV Master Bedroom Install circuit for TV and Cable for TV Living room- Supply and install new circuit for outlet behind tv Dining Room- Supply and install (1) LED can lights Install chandelier in new location above dining room table Install dimmer switch for chandelier Pantry Supply and install dedicated circuit from panel for wine cooler
1)â€”â€”Remove 100 amp fused main disconnect. 2)â€”â€”Remove double tapped sub panel below main disconnect. 3)â€”â€”Install 125 amp 8/16 circuit main breaker panel. 4)â€”â€”Install 10*10*8 inch PVC junction box at branch circuits that were in old sub panel removed. 5)â€”â€”Extend all outdoor branch circuits from junction box to new 125 amp main breaker panel. 6)â€”â€”Install whole home surge protector. 7)â€”â€”UPDATE GROUNDING; Install 2 new ground rods, 1 water pipe ground and 1 low voltage ground bridge interconnected with #4 gauge bare copper wire. 8)â€”â€”Label panel and clean area.