Jeff, the tech from Midwest came yesterday to do the spring clean up of the furnace and AC. He came at the arranged time, took care of what needed to be done, kept me informed of what he was doing. Mark, the owner and his crew installed the new furnace and AC about 5 years ago, it's been nice to have someone I can trust to maintain the equipment. Brian in the office is great to work with in scheduling appointments. You guys are great
Very pleased with scheduling with Brian and the work done by Jeff is awesome!
Jeff did a very good job. Good careful professional work.
Great Service Thank You
Always good service and fair prices
Mark is an excellent communicator. He quickly diagnosed the issue and fixed our system. I can’t speak highly enough!
Diagnosed problem and quick resolve
Clean and check Goodman air conditioner in Mt Prospect. AC tune-up on condenser with a very dirty coil.
Installed EZ Trap condensate drain trap to stop AC water leak in Mt Prospect.
We installed a Ducane 80% model 80g1 and a 13 seer air conditioner.
Furnace installation. We installed a Ducane 80% model 80g1e furnace.
We serviced a Air conditioner and performed ac cleaning. We recharged the refrigerant r22 freon
Clean and check with preventative maintenance on AC unit. 21 point HVAC inspection found low dual capacitor. Replaced capacitor and cleaned outdoor condenser.
Preventative maintenance AC clean and check. Replaced filter on Aprilaire 1210 model whole home air purifier. Cleaned outside condenser and checked pressures/subcooling.
Ac service and maintenance. We performed cleaning on the Bryant air conditioner s
Air Conditioner maintenance and cleaning. Found low dual capacitors and added a hard start kit to unit with loud compressor and hi in rush amps.
Air conditioner installation. We installed a Ruud ra13 ac and ADP coil
Preventative maintenance with 21 point inspection on Air Conditioner and AC. Flushed out condensate lines and checked pressures and subcooling on AC system. Cleaned and washed condenser.
Diagnosis on no cool. AC not running, found low voltage short and blown fuse. Found short, rewired and replaced fuse on circuit board.
Air condition diagnosis for no cooling found a blown dual capacitor from a mouse. Replaced capacitor on Trane condenser now homeowners are cooling.
Service call for HVAC AC air conditioner not cooling. Diagnosis Found flat system and recharged per clients orders.
HVAC installation. We installed a Ruud 96% u96v 2 stage variable furnace and ra14 air conditioner.