Mark is an excellent communicator. He quickly diagnosed the issue and fixed our system. I can’t speak highly enough!
Diagnosed problem and quick resolve
Very knowledgeable techs, with great service and reasonable prices
This company gives you honest answers, were very quick to getting to my home and fixing my boiler’s issue. Highly recommend them and we will use them again.
Jeff was awesome! He was quick to arrive, very thorough & took the time to show me the problem
The service tech refurbished most of the decaying and leaking parts on my humidifiers. Went from leaking and corroded, to looking and operating like brand new!
These guys have always been good about coming out in a timely fashion whenever we’ve had issues. Great to feel confident they have you covered.
Heating repair. We serviced a Peerless boiler. We replace the pressure reducing and pressure relief valve.
Annual furnace maintenance on two Heil furnaces. Replace Aprilaire humidifier pad in Medinah.
Furnace replacement We installed a Ruud r801s single stage furnace
Diagnosis on Aprilaire 700a. Cover wasn't on correctly leading to uncomplete connection at molex plug inside* outdoor temp sensor was dialing down RH due to low outdoor ambient temps.
Payne 80% gas furnace diagnosis call for noise. Found aging inducer with play in the wheel, high amo draw and bad bearings. Quoted new unit as furnace is 14 years old and oversized.
Humidifier installation. We installed an Aprilaire 600 humidifier with outdoor sensor
Installed April Aire 700m and 600m humidifiers
Double preventative maintenance clean and check. Current humidifiers not working, relative humidity of 19% inside. Bryant 90% gas furnace. Installing new Aprilaire bypass humidifier on downstairs unit, and powervent for upstairs 80% Rheem furnace.
Burnham boiler no heat call. Found bad circulator pump.
Furnace maintenance.. We cleaned 2 Trane furnaces and serviced the general humidifiers
Carrier 80% gas furnace with Aprilaire 600 automatic humidifier. Did preventative maintenance and clean and check. Also replaced humidifier pad and reccomend blower wheel assembly cleaning and honeywell uv bulb to help with dust and allergies.
Carrier infinity 80% gas furnace counterflow preventative maintenance and cleaning done. System operating well, customer expressed interest in a Aprilaire media filter upgrade. And possible Aprilaire humidifier 700 as house was very low on relative humidity.
Furnace installation. We installed an 80% Ruud R801s Furnace