I have been a customer of Morehart A/C & Heating for almost 6 years, and have been very pleased with their service and products, including my purchase of a complete York A/C and heating system, and Apco Aire unit. The technician who usually comes to my home twice a year, Tom G, is very professional, competent, and knowledgeable. He is also respectful, courteous, prompt, and provides detailed information of his findings during each of his visits. I am never left in doubt about the work that has been done. In the past, I have used other companies; however I find Morehart A/C & Heating to be a step above the others in providing great customer service and quality products.
In Sun Lakes, AZ performing a heating maintenance service to an Amana unit. Replaced air filters and did a safety inspection to the heating portion of the unit.
In Sun Lakes, near East Crystal Drive and South Granite Drive performing Fall preventative maintenance on 2 Amana furnaces. Completed services in accordance with maintenance checklist. Upon departure, units are working properly and within manufacturer specifications.
In Sun Lakes, AZ: DIAGNOSTIC- On arrival, found system running and cooling. Checked Freon levels; all in factory specification. Checked volt and amp draws; also within factory specification. Capacitor is new and in specification. Checked drain line and wet switch; no water, and drain is clear. Checked indoor blower motor; amps are good. Checked split temps; Return 78/Supply 59. Found ECO+ enabled so when customer left, system over rode program.
In Sun Lakes, AZ: Completed service in accordance with maintenance checklist. System is 25 years old and in very poor condition. Recommend replacement of entire system. Replaced capacitor during service due to it being swollen and testing at 0. Made customer aware of wear to system.
In Sun Lakes, AZ: Upon arrival, found 45/5 capacitor failed causing compressor to not cycle. Replaced part, cycled system, unit working properly. Checked other system capacitor at time of service. It is within 5%.
In Sun Lakes, AZ: UPON ARRIVAL CYCLED UNIT INTO COOLING MODE. CLEANED AND WASHED CLEAN EFFECT AIR FILTRATION . TOOK TEMPERATURE READINGS FROM SUPPLY AND RETURN. AT UNIT CLEANED AND TIGHTENED ELECTRICAL CONNECTIONS. TOOK VOLTS AND AMP DRAWS FROM COMPONENTS. CHECKED FREON LEVELS WITH SUPER HEAT AND SUBCOOL. UPON DEPARTURE UNIT WORKING PROPERLY AND WITHIN MANUFACTURER SPECIFICATIONS.
In Sun Lakes, AZ: UPON ARRIVAL CYCLED UNITS INTO COOLING MODE. REPACED TWO 16x25 INTAKE FILTERS. AT UNITS CLEANED AND TIGHTENED ELECTRICAL CONNECTIONS. TOOK VOLTS AND AMP DRAWS FROM COMPONENTS. CHECKED FREON LEVELS WITH SUPER HEAT AND SUBCOOL. CHECKED STAR AND RUN CAPACITORS. WASHED AND RINSED OUTDOOR COILS. UPON DEPARTURE UNITS WORKING PROPERLY AND WITHIN MANUFACTURER SPECIFICATIONS.
In Sun Lakes, AZ: Completed service in accordance with maintenance checklist. Please refer to list for photos and ratings. Systems working properly upon departure. Customer recently purchased home from the Knudson family. Went through filter location and warranty with customer. Contacted manufacturer to inquire about warranty transfer. They requested information from new homeowner on purchasing home and our invoice with system model and serial numbers. Updated profile to reflect information. CC Mike with warranty info. Listed pricing in estimate attached to invoice about service plans.
Service in Sun Lakes,AZ for an existing customer!
Performing heating/cooling maintenance on 16 seer Amana package heat pump in SunLakes Arizona
Changing out a old York coil and installing a new York coil with some new R410a near the Ironwood Country Golf Club area right off of Riggs Road.
Out in Sun Lakes where I found a run cap that was swollen and needed to be replaced. Unit is up and running and customer is happy!
In Sun Lakes on another break down . This York split system had a frozen evaporative coil .
In Sun Lakes servicing a unit we have serviced for 8 Years customer is a maintenance agreement holder all is well!