In Waddell, near West Cheryl Court and North 159th Avenue performing a diagnostic on a unit that is making strange noises. Upon arrival, found disconnect off. Turned on system. Unit is working properly. Customer wanted thermostats set to higher heating temperatures. Set for customer.
Installing a kitchen hood vent in a new custom home off of the loop 303 and w waddel rd
In Waddell, near West Townley Court and North 192nd Avenue performing seasonal preventative maintenance on 2 American Standard package units. Due to age and condition of systems, I would recommend upgrading units. Left customer with estimate pricing.
In Surprise, AZ: COMPLETE SYSTEM INSPECTION- Customer is going to have another technician supply report for system inspection.
In Waddell, AZ: DIAGNOSTIC- Upon arrival, cycled unit into cooling mode. Found pressures low on condenser. Checked for leak and found one at RXV fitting on air handler. Tightened fitting and recharged system. At time of service, recharged right to specification and ran out of Freon. If homeowner calls back, recharge system to correct specification.
In Waddell, AZ: FOUND RUN CAPACITOR BAD. NEEDS NEW 45/5/440 CAPACITOR. INSTALLED NEW CAPACITOR UNDER PARTS AND LABOR WARRANTY.
Finishing up at a custom home in Waddell, Az
Finishing up duct work at a custom home in Waddell, Az
Installing new Goodman systems at a custom home build in Waddell, Az
Installing the 2nd Goodman unit and duct runs at a custom home in Waddell, AZ.
New custom home putting first unit up in Waddell, Az
In Waddell servicing a customers 2 Heat pump systems. Checked volt and amp draws. Checked Freon levels. Tightened all electrical connections. Changed the return air filters and washed the outdoor coils. Both units are Ready for the cold.