Upon arrival the technician found that the primary drain line was clogged. This is causing water to drip into the pan, The secondary line coming from the pan is currently leaking due to a nail from the roofing replacement. Replace the system in 2020 and the roof was replaced in June 2021. The customer did not know about the roofing now until she had an issue with her drain lines. The technician cleared out the primary drain line, and installed an SS one float switch. The system is working properly at this time but the secondary drain line will need to be replaced. And the sheet rock will need to be replaced by the roofing company, as well as the secondary drain line should be paid for by the roofing company due to the damage.
Upon arrival the technician performed a pre-season AC inspection. The technician began in the attic checked over the furnace and coil. The technician checked over the drainage, and finally checked the capacitor and blower motor. Furnace and coil working properly at this time. The technician went out to the exterior unit. And checked the pressures, as well as electrical including big capacitor, compressor, and fan motor. System checks out at this time. System working properly at this time.
Upon arrival technician found that the condenser was not on. Upon further investigation the technician checked the capacitor and found that the capacitor had blown. The technician recommended a new 45 x 5 capacitor to replace the failed capacitor, and installation of a hard start kit. The customer stated that he needed me to diagnose the issue and he will get a capacitor and hard start kit and install them. The technician left the failed capacitor with the customer. System not working properly at this time.
Upon arrival of the technician insulated be hot and cold line of the water heater as well as the drain line.
Plumber installed kitchen sink faucet and tested proper operation. I was also able to clear a restriction in the natural gas orifice restoring proper operation to the stovetop at no additional charge. I also advise the homeowner that they need to contact a fireplace repair company to determine the issue with their natural gas fireplace. We will order and return to install whole house water filtration system to be located on the front right corner of the house where the water enters the home from the meter. The homeowner is going to purchase a new dishwasher and will have it here for us to install when we return to install the water filtration system.
Replace existing natural gas water heater with a new natural gas water heater of like size and capactity. Including new gas line and new copper supply lines.
Upon arrival technician found that the igniter was not striking properly. Only at a certain angle does the igniter work properly. The technician after 20 minutes of attempting to light the water heater was able to successfully like a water heater. The technician recommends replacement of igniter and thermal couple. Water heater is lit and working properly at this time.
Upon arrival the technician spoke with the homeowner about the situation That was going on, the homeowner stated that two companies came out, one company said it was in the coil. The other company said it was in the filter line dryer. The technician that said it was in the filter line dryer, replaced that filter line dryer. So I do not know whether it was originally leaking from there or not. The technician that came out and replace the filter line dryer, also charge the system. The technician checked the charge on the system, the system charge was low. Also the Delta T was only at 10Â°F. The technician went upstairs to the coil and found that the coil had been previously opened. Technician re-opened up the coil and found that indeed the coil is leaking. The technician does not know whether or not the filter line dryer was originally leaking, but the coil is.
My Guys Heating & Air Conditioning installed a brand new 3 Ton A/C system for Ms. Snider as well as an additonal duct in the living room and relocated the return air intake all of the work was completed in 1 day.