They were very friendly and knowledgeable. Did a very neat job
Prompt, friendly,all busness
INSTALL 4 TON 3PIECE CONVER DUEL FUEL 10YR P 5 YR L. MADE SURE SYSTEM WAS INSTALL PROPERLY. CHECK GAS PRESSURE AND FOR PROPER VENTING. CHECK THERMOSTAT, AIR FILTER, CHECK ALL ELECTRICAL CONNECTIONS. MADE SURE WORK AREA WAS CLEAN WHEN FINISH. EVERYTHING IS WORKING GOOD.
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK ALL ELECTRICAL CONNECTIONS, CHECK CONDENSER COIL, CHECK DRAINAGE, CHECK FREON LEVELS, CHECK AIR FILTER. LUBRICATE ALL NECESSARY MOVING PARTS, ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK CONDENSOR COIL, ADJUST BLOWER COMPONENTS, CHECK THERMOSTAT, LUBRICATED ALL NECESSARY MOVING PARTS CHECK FOR PROPER ENERGY CONSUMPTION. EVERYTHING RUNNING GREAT.
Checked ducts for build up.
Checked ducts for build up, cleaned condensation drain and condensing coil, no repairs needed.
Checked thermostat for wear, cleaned condensation drain. No repairs needed.
Cleaned and safety checked the Heil 2015 air condensing unit with heat pump. Checked ducts, no repairs needed.
Cleaned and sanitized the Heil 2015 air conditioning unit with Zep con-coil cleaner, no repairs needed.
Cleaned and sanitized the 2012 Air conditioning unit with condensing pump. no repairs needed
Cleaned and Service 2004 trane unit.