Prompt, friendly,all busness
CLEAN AND CHECK CONDENSOR COIL, ADJUST BLOWER COMPONENTS, CHECK THERMOSTAT, LUBRICATED ALL NECESSARY MOVING PARTS CHECK FOR PROPER ENERGY CONSUMPTION. EVERYTHING RUNNING GREAT.
Checked ducts for build up.
Checked ducts for build up, cleaned condensation drain and condensing coil, no repairs needed.
Checked thermostat for wear, cleaned condensation drain. No repairs needed.
Cleaned and safety checked the Heil 2015 air condensing unit with heat pump. Checked ducts, no repairs needed.
Cleaned and sanitized the Heil 2015 air conditioning unit with Zep con-coil cleaner, no repairs needed.
Cleaned and sanitized the 2012 Air conditioning unit with condensing pump. no repairs needed
Cleaned and Service 2004 trane unit.