Professional experience. Thorough explanation of service.
We had a great first experience. Our AC unit is old and has been on the way out. The technician went over all of our options on repairs/replacement and we were able to make our choice from there.
Called and came out the same day.
Trustworthy, thorough & efficient!
Installation Inspection on new installation of Carrier Furnace.
Semi annual (FALL) Scheduled Maintenance on CARRIER furnace. Customer has crack in heat exchanger. Talked with Customer about problem. She decided to just replace system due to the age.
Replaced flame sensor on York Furnace.
Diagnostic service performed on the Gas Trane Furnace unit. Confirmed that the system is working within manufacturer specifications. Pictured is the customer's Gas Trane Furnace Unit.
Performed tuneup on Trane furnace. During inspection, found that water had been leaking during the summer which caused rust on burners and inside cells on heat exchanger. Inducer motor was over amping and a capacitor needed replaced. Recommended new unit due to the damage, customer opted for capacitor replacement.
Performed tuneup and inspection on Carrier furnace She has a dynamic 24v electronic filter that required special filter to be installed inside. Need to order this. Humidifier pad was very dirty and has been changed
Tuneup and safety check on Bryant furnace. The system is operating properly and is ready to heat this winter season.
Diagnostic service performed on the Rheem Gas Furnace unit. Confirmed that the system is working within manufacturer specifications. Pictured is the customer's Rheem Gas Furnace Unit.
Bryant furnace not keeping up with thermostat. Found furnace blinking pressure switch fault. Checked trap, water is backing up in the secondary. Drained all water.Cleared trap. Cleaned flame sensor.Operating in heating at this time.
Semi annual (FALL) Scheduled Maintenance on Carrier "Infinity Series" Variable Speed 3 Ton Electric Furnace.
Semi annual (FALL) Scheduled Maintenance on Comfortmaker furnace.
Semi annual (FALL) Scheduled Maintenance on CARRIER furnace.
Diagnostic Service Call on Carrier Electric furnace. noise issue. The noise customer is hearing the defrost cycle. All ok.
Diagnostic service performed on the Ducan Gas Furnace unit. Confirmed that the system is working within manufacturer specifications.
One of our talented technicians went to the customer's home to give an estimate on a replacement part for their Gas Carrier Furnace Unit. Pictured is the customer's Gas Carrier Furnace Unit.