We had a great first experience. Our AC unit is old and has been on the way out. The technician went over all of our options on repairs/replacement and we were able to make our choice from there.
Called and came out the same day.
Trustworthy, thorough & efficient!
Diagnostic services performed on a 2002 Air Conditioning System. Free estimate provided at customer request to install a Carrier 13 SEER 3 Ton Air Conditioner. Included a one year service maintenance agreement and new Honeywell T1 Thermostat.
Performed tune up and check out on COMFORTMAKER A/C UNIT.
Compressor and fan capacitor replaced on 1988 Rheem Air Conditioner. System is working within manufacture specifications at this time.
Minor A/C repairs made on a 1988 Rheem unit. Replaced the dual capacitor and fuse and system is fully operational at this time.
Performed semi annual scheduled maintenance on CARRIER A/C unit. Checked all settings, pressures, general cleaning of unit, replaced filter if needed, performed overall visual inspection of unit.
Performed semi annual scheduled maintenance on Carrier A/C unit. Checked all settings, pressures, general cleaning of unit, replaced filter if needed, performed overall visual inspection of unit.