Professional experience. Thorough explanation of service.
We had a great first experience. Our AC unit is old and has been on the way out. The technician went over all of our options on repairs/replacement and we were able to make our choice from there.
Called and came out the same day.
Trustworthy, thorough & efficient!
Upon inspection, found the upstairs thermostat faulty unable to turn anything on. Customer requested to replace both thermostats due to being same age. Installed two Honeywell T6 Pro Programmable Thermostats.
Diagnostic service performed on Lennox Gas Furnace to find the gas was turned off. Turned on the gas and confirmed the system is running properly.
71891 Thank you for business and we greatly value your review!
Diagnostic Service Call for A/C. Customer stated nothing would turn on. Found breaker for the air handler tripped. Reset breaker and cycled system in cooling. All components working properly with a 18 degree temp drop. Cycled system in heating mode. Tech could not get system to trip breaker. System operating properly at this time.
2012 UPG Air Conditioner diagnostic service appointment. Unable to service unit due to frozen coil. Rescheduled to come out next day once coil thaws out.
Capacitor blown on outdoor condenser for central air system. Customer approved repair so replaced the Dual Capacitor 35+5 and system is now cooling properly.