Excellent service and advise on what we need to review. I would recommend this service highly.
Technician diagnosed faulty circuit board that was shorting out on a Comfortmaker furnace. The customer chose to attempt to purchase a board on his own and repair it himself.
Replaced in warranty part on BRYANT furnace. Intake Nipple Kit
Diagnostic Service Call on 2015 Bryant Furnace
Leak at discharge line connecting to the condenser repaired and nitrogen level tested. System performing within manufacture specifications.
Performed diagnostic service on Bryant a/c unit. System low on refrigerant due to a leak right at the discharge line connecting to the condenser. filled system for temporary cooling until leak can be fixed.
Service call on TEMPSTAR a/c unit. Unit not cooling found 70/5 capacitor with no charge and disconnect with some light damage.
Goodman 1999 unit was froze over, thawed out added contractor and 2 pounds of freon
Replaced the evaporator coil on a 2017 Carrier Air Conditioning System.
performed service on TRANE A/C unit. Checked pressures from winter install.
added 2lbs. R410a to AC unit
Upon diagnostic visit, found unit sub cool at 1.0. Previous owner did install is AC themselves. No paperwork on install. Not sure if vacuum pump was used or how the install went. Came to the conclusion that the unit wasn't properly charged at time of install.