Excellent service and advise on what we need to review. I would recommend this service highly.
Leak at discharge line connecting to the condenser repaired and nitrogen level tested. System performing within manufacture specifications.
Performed diagnostic service on Bryant a/c unit. System low on refrigerant due to a leak right at the discharge line connecting to the condenser. filled system for temporary cooling until leak can be fixed.
Service call on TEMPSTAR a/c unit. Unit not cooling found 70/5 capacitor with no charge and disconnect with some light damage.
Goodman 1999 unit was froze over, thawed out added contractor and 2 pounds of freon
Replaced the evaporator coil on a 2017 Carrier Air Conditioning System.
performed service on TRANE A/C unit. Checked pressures from winter install.
added 2lbs. R410a to AC unit
Upon diagnostic visit, found unit sub cool at 1.0. Previous owner did install is AC themselves. No paperwork on install. Not sure if vacuum pump was used or how the install went. Came to the conclusion that the unit wasn't properly charged at time of install.
Free in home estimate for Carrier AC equipment
Recharged a 2017 Bryant AC with 4 lbs of R-410A Puron and added Easy Seal as system was low on refrigerant.
Recharged a 2017 Bryant Air Conditioner with 4 lbs of R-410A Puron and added Easy Seal.