Paul was friendly and knowledgeable
Professional,on time, good work .
The serviceman came in and quickly assessed the problem with my HVAC system. He immediately took control of the situation at hand and resolved the problem within an hour or less. It's could to see someone put their knowledge and skills to work to take care of a customer's needs. I am very pleased with Roussos' Air Conditioning.
Michael was professional, knowledgeable, and personable. He troubleshot my A/C unit and isolated the problem in a matter of minutes and had it fixed with a quickness. He communicated the problem and solution with me before proceeding with any maintenance. He was very personable and made me feel comfortable chatting with him. I would highly recommend.
I would like to say how professional of a company!! Jacob was AWESOME!! Thank you for being a top notch company.
... professional and knowledgeable employees... Especially appreciate they were able to help during an emergency situation on the weekend days as I’m a single father of a little boy and the unit must remain in working order... this review is on the behalf of Jacob Thompson and others...
Prompt service friendly
Michael was a great representative for your company. Very professional and personable and took care of my issue quickly and efficiently. Would definitely refer all my family and friends to your company after the customer service I received from Michael.
Hvac tech Paul was very knowledgeable and friendly. Got here, went right to work taking care of our problem. Thanks Paul
Perform air conditioning maintenance tune-up on ICP package unit heat pump system.
Perform air conditioning maintenance tune-up on Goodman heat pump system.
Performed HVAC tune up on Gibson heat pump system.
Performed tune ups on 2 Rheem heat pump systems.
Found Honeywell thermostat not setup properly. Setup thermostat and checked system for proper operation. Also installed another Honeywell thermostat for customer.
Replaced blower motor under parts and labor warranty
Repaired water leak on attic system
Found a bad float switch on a Comfortmaker split system heat pump. Replaced switch and checked refrigerant levels also flushed drain line and added cleaner.
Cleaned drain line and verified system was draining properly
Found a bad capacitor on a American standard split system heat pump. Replaced capacitor and checked refrigerant levels. Found system low on refrigerant. Recharged system and checked system for proper operation.
Replaced warranty dual capacitor on Heil Heat Pump system.
Found a bad capacitor for the condenser fan motor on a Rheem split system heat pump. Replaced capacitor and checked system for proper operation.
Found broken start wire to compressor on a Trane split system heat pump. Rewired and checked system for proper operation. Found hard start relay had fail and run capacitor to be under performing. Replaced both hard start and capacitor.