Michael was a great representative for your company. Very professional and personable and took care of my issue quickly and efficiently. Would definitely refer all my family and friends to your company after the customer service I received from Michael.
Hvac tech Paul was very knowledgeable and friendly. Got here, went right to work taking care of our problem. Thanks Paul
The Roussos Team is THE benchmark for professional and courteous service in Bay County! My first experience with them was back in April of 2014 when they replaced the HVAC systems on the house we had recently purchased when we moved from Andrews AFB in Maryland to Tyndall AFB. Mr. Pat Boykin and his team answered every question we had and kept us informed through every step of the installation process. Since then, they have continued to take care of us, our HVAC systems, and our home in general. If I could rate them higher than five stars, I would give them ten! They are simply that fantastic!
Derrick did a great job, even called me back the next day when I thought I had a problem. I rated convenience a little low, because I live 1 1/2 hours away and scheduling was an issue, but we got it done.
Paul, from Roussos Air Condition, did an outstanding job repairing my furnace. He was very knowledgeable and explained what and why he was performing each task. He is a true asset to Roussos and the Panama City community.
The tech was on time clean appearance knew what he was doing at a reasonable time.....ty Roussos
Kevin Bowlin did excellent job and spend a couple hrs checking my old system
Paul came out to diagnose & repair our Nest Thermostat. He came out twice & you were able to schedule us in after 5pm, which made my pregnant wife very happy! Thank you Paul & everybody else who helped get us cool again!
Perform air conditioning maintenance tune-up on Amana gas furnace straight cool system.
Pulled and cleaned evaporator coil on Rheem split system heat pump. Recharged system and added leak dye. System is operating properly at this time.
AC Repair, Refrigerant Leak
Found reversing valve not wired up at condensing unit on Goodman split system heat pump. Bad consider wires from air handler. Rewired with spare wires and energized reversing valve. Checked system for proper operation.
Perform air conditioning maintenance tune-up on Carrier straight cool system.
Found leak in evaporator coil recharged system. Checked system for proper operation.
AC Repair, Ductwork Repair. Low refrigerant
Perform air conditioning maintenance tune-up on Carrier gas furnace straight cool system.
Perform air conditioning maintenance tune-up on Goodman straight cool system.
Perform air conditioning maintenance tune up on Trane gas furnace straight cool system.
Perform air conditioning maintenance tune up on Trane gas furnace.
Found Rheem split system heat pump to have dirty filter. Checked system out complety and checked for proper operation.
Pull and Clean Evaporator Coil. Ac Maintenance. Ac repair.
Found Goodman split system to be out of refrigerant. Performed leak detection could not pin point leak. Added leak dye to system and checked system for proper operation.