First rate job of replacing filter-drier and manifold. Very pleasant person, completed job quickly, got unit back on line quickly.
Would recommend them to all my friends and family.
Paul Evans / Roussos Air Conditioning provided service for our AC system. Paul showed up when he said he would. He did a thorough check of my system. Fortunately we didn’t have a serious problem. Paul did a great job!!
I will recommended your company as the best.
I called right at closing on Friday, and they had a technician at my house Monday morning--and this was just for maintenance! Andrew was my technician, and I received grade-A customer service. Andrew was courteous, a good conversationalist, and he taught me a lot about my AC unit so that I can take good care of it and get the most from it. I love this company!
Paul was friendly and knowledgeable
Professional,on time, good work .
The serviceman came in and quickly assessed the problem with my HVAC system. He immediately took control of the situation at hand and resolved the problem within an hour or less. It's could to see someone put their knowledge and skills to work to take care of a customer's needs. I am very pleased with Roussos' Air Conditioning.
Michael was professional, knowledgeable, and personable. He troubleshot my A/C unit and isolated the problem in a matter of minutes and had it fixed with a quickness. He communicated the problem and solution with me before proceeding with any maintenance. He was very personable and made me feel comfortable chatting with him. I would highly recommend.
Perform air conditioning maintenance tune-up on Rheem heat pump system.
Perform air conditioning maintenance tune-up on American Standard heat pump system.
Replaced condenser wire and checked system for proper operation.
Perform air conditioning maintenance tune-up on Carrier heat pump system.
AC service, AC repair
Perform air conditioning maintenance tune-up on Goodman heat pump system.
Perform air conditioning maintenance tune-up on comfort product straight cool system
Perform air conditioning maintenance tune-up on Gibson heat pump package unit.
Found condensing unit running with no signal to it. Contactor was stuck replaced contactor and checked system for proper operation.
Found two Nest thermostats not functioning. Replaced nest thermostats and checked system for proper operation. Systems are cooling properly at this time.
Perform air conditioning maintenance tune up on American Standard heat pump system.
Found 2nd and 3rd floor systems to have bad transformers. Replaced transformers and found 3rd floor system to also have burnt wires and a bad outdoor capacitor. Replaced all parts and checked system for proper operation. System is cooling properly at this time.
Perform air conditioning maintenance tune-up on Goodman straight cool system.