Tech was very professional. Kept me informed of the issue and provided options. Reported a long standing issue that was not discovered previously. Very thorough. Thank you.
The technician was very pleasant and personable and on time. He gave the system a very thorough check up. It was a pleasant experience.
Great Technician, Very Polite and Knowledgeable!
Very professional and knowledgeable. Great attitide
Fast to get a serviceman out there and he was very knowledgeable and quick to diagnose and repair.
Michael did a great job diagnosing our problem. He was very nice and knowledgeable. We're very pleased with his service.
Paul did a great job on the annual servicing for our two systems
Micheal came late at night and did a quick and amazing job
Preforming maintenance tuneup on new Comfortmaker AC heatpump for a valued Roussos customer.
Found rheem split system heat pump not wired to operate as a heat pump. Replaced thermostat and wired system properly to operate as a heat pump.
Perform air conditioning maintenance tune-up on Comfortmaker heat pump system.
Found leak on suction line service port fixed leak and added 16 lbs r22 refrigerant to Westinghouse split system heat pump. Checked system for proper operation.
Perform maintenance tune-up on Rheem heat pump system.
Performing AC maintenance tuneup on a courier air handler and Goodman condenser unit for a valued Russo‘s AC company customer. Adjusted charge to increase efficiency of Ac unit.
Perform air conditioning maintenance tune up on York heat pump system.
Performance maintenance AC tuneup on 1 year old Comfortmaker heat pump AC unit for Roussos Valued Customer.
Found Mitsubishi mini split system not operating. One head not in sync with the others re synced head and checked system for proper operation.
Replaced control board and heat relay
Perform air conditioning maintenance tune-up on Carrier heat pump system.
Perform air conditioning maintenance tune up on Goodman straight cool system.
Added refrigerant to system found leak in the evaporator coil.
Replaced muffler on condensing unit
Perform air conditioning maintenance tune-up on York heat pump system.