Troubleshot outlets on kitchen counter not having power. Found loose wire and fixed it. Outlets work as they should. We furnished, wired, and replaced the gfi for said outlets. Performed panel maintenance and tightened all connections. During panel maintenance, we found and fixed neutrals bundled up under the same lugs. We furnished, wired, and replaced 2 unlisted breakers in the panel as well.