Service was great as always.
Josh was great
Response from Sears Heating & Cooling:
Thank you for your review!
Replaced failed contactor and cleaned up wiring terminal ends
Performing maintenance on a. 1993 Armstrong air conditioner.
Scac capacitor is 40/5 and I replaced due to being at 36/5
Unit not cooling elk 80 degrees inside Lo on charge Added r410 Replaced voltage absorption system Cleaned outdoor unit and tightened wiring 140 low 330 high 15 superheat 20 split temp Pulling humidity out Moving soon
Replaced faulty capacitor, hard start kit and water protection system for second floor mechanical room installed
Performing maintenance on a 2016 comfort maker air conditioner
2019 York air conditioner. Unit has thawed. Check pressures and they are good. All electronics are within specs unit is 2 years old. Customer mentioned they had changed the filter before I came and it was very dirty. Dirty filter caused lack of airflow causing the coil to freeze and with it being as frozen as it was unit need to that before running it after changing the filter. Temp split is 18 degrees. Let customer know to change filter one a month. All okay at this time.
Performing maintenance on a 2012 Bryant air conditioner.
2002 trane ac 10 seer. Clean and check. Good to go
Customers thermostat showing low battery. They said they’ve tried several batteries and it’s not helping. Fan will run when setting the fan on I will not call for heating or cooling. Provided options for thermostats on page hh5. I wanted to go with T4 pro thermostat. Cycled system on heating and cooling. Showed customer thermostat operation. Customer will set schedule up later. Gave customer,er user guide for thermostat. All okay at this time.
Ac check on system. Cleaned unit r410. Replaced 213 filter.
Ac check on rheem 1993 like a boss. Cleaned system. Furnace is a propane lit set up on a.2 stage new Bryant from 2020. With I wave and humidifier
Customer opted to have me install new thermostat for option ho1a. Installed thermostat and helped him set it up. Provided estimate for 50 gallon hot water tank with expansion tank for $1619 plus $110 for expansion tank. Customer wanted to proceed with have new tank installed today. Completed water heater installation and air conditioner check.
1994 Lennox air conditioner. Customer mentioned temperature on thermostat not going down when she turned on the ac. Found voltage distribution center failed and not allowing voltage pass and fire up the condenser unit. Showed options for repair on page Hd3. Customer chose hd3a. Completed repair and cycled unit. All okay at this time.
Performing maintenance on a 2011 Bryant, air conditioner