Josh did a great job! He showed up on time, checked everything in my furnace and was done in 30 minutes.
This was our annual Furnace maintenance agreement. Josh was respectful and very informative. He took time to explaine the settings on the humidfier. Seemed to have done a thorough job.
Josh was such a treat to welcome into our home. He was incredibly kind and knowledgeable. Individuals like Josh make us want to rely on Sears for all our heating and cooling needs. Thank you, Josh! Cost was also great!
Joshua diagnosed the problem quickly and accurately and was able to make the repair promptly. It's always nice to have someone competent, and it's even nicer when he or she is personable. Joshua was both. (He even carried a small treat for the dog!)
Josh took care of our heating system on a timely, no nonsense basis.
Josh was excellent. Very attentive to the problem & solved it!
No heat situation with unit badly in need of cleaning. Performed maintenance and ran combustion test to ensure safe and operation.
Propose cost of installing high-efficiency furnace
Furnace repair on maintenance inspection including cleaning necessary components, tightening electrical connections and combustion analysis to ensure safety.
Furnace repair on maintenance inspection including cleaning necessary components, tightening electrical connections and combustion analysis to ensure safe and efficient operation.
Performed furnace maintenance and safety check on Bryant unit
Bad exhaust system. Replaced exhaust system and voltage absorption system 7.5 Tightened up wiring
Performing maintenance on a 2002 comfortmaker gas furnace.
Furnace repair on no heat situation, replaced ignition module and capacitor. Cycled operations and ran combustion test to ensure safety.
New furnace and air conditioner estimate in Hilliard, Ohio.
Performing maintenance on a 2020 comfortmaker gas furnace.
Replaced furnace filter at customers request
Installed Iwave air cleaner to customers Bryant furnace to improve air quality
Rtu unit in Grove city. Bryant 2017 two stage system 16-20-2. Needed 4 of them
Completing maintenance on a Ruud gas furnace
1998 trane gas furnace. Upon arrival customer mentioned she turned unit up to 69 from 65 and unit did not kick on. When I set the thermostat it was set at 63 with a room temperature of 66. After I set thermostat to call for heat sensor unit fired up and ran normal operation. Ran performance testing on unit. Temp rise is 45 degrees. Combustion analysis showed 2 ppm CO/ 8% O2/ 330 degrees stack temp. Filter is in good shape and is a 201. Tested thermostat within one degree and found no issues with thermostat. Thermostat slightly confusing to read and could have been read backwards. Discussed thermostat operation with customer. Checked components in unit and found voltage absorption system for air movement motor out of specs. Recommended replacement to prevent premature failure of motor. Showed options on page hn4. Customer chose hn4c. Replaced voltage absorption system and upgraded. Replaced ignition system and upgraded. Cycled unit several times. All okay at this time.