Our family has trusted Sears Heating and Cooling for decades
Very professional and efficient.
They are very professional and took all the steps to protect all of from Covid19 while they were here.
I continue to receive great service, and this time when our air conditioning went out on the weekend. After some attempts to verify on my own this wasn't just a lockup I called SHC on Sunday morning at 8:45 AM and Wally called me back 2 minutes later to let me know he has my call and will be his second stop. He arrived about 90 minutes later and diagnosed the issue and repaired it (bad capacitor) in under 30 minutes.
Always good service
Proposed installation of air condition
Air conditioning and furnace maintenance clean and check
How did leak sealant and charged unit to manufacture specified range, on a train air conditioner
AC check out on a 1982 general electric air conditioner.
1991 rheem furnace. Found blower not running. Voltage absorption system is good. Currently getting 120 volts to motor. Motor is bad. Offered options for repair on page hc6. Customer also wanting information for replacing system. Ballpark estimate for replacing full system is $6200-$7500. Customer also would like to receive options for repair via email.
AC check out on a 2010 Bryant air conditioner. Completed performance check, safety check, mechanical check. Everything is working properly at this time.
Annual maintenance on Rheem air conditioner
Replace leaking Evaporator coil
Customer mentioned unit not keeping up with thermostat on very hot days. Checked temp drop found it at 19 degrees. System Has fixed bore metering device. Filter is clean. Blower is not randomly shutting off. Indoor wet bulb is 74. Entering ambient to unit is 78. Voltage absorption system is good. Found distribution center with contacts badly pitted and burned. Coil is very dirty on unit. Found refrigerant charge low and dirt on coil keeping pressure high enough to achieve some cooling. Unit is 34 years old. Offered options for charging unit with refrigerant and offered option for an estimate to replace. Customer would like to have an estimate. Scheduled Wednesday the 22nd at 8am.
AC check out on a 2013 Bryant air conditioner.
Customer wants to relocate condenser location to the other side of house away from master bedroom. Besides the permit fee for HVAC it requires an electrical permit fee. This is possible by code. Proposed installation of Bryant evolution system with condenser installed on other side of house
Plat check. Filter is dirty, they had extra one. Now clean 16-25-1 Outdoor electrical is good Outdoor system is dirty and should be cleaned off twice a year due to dryer vent. Shown options for cleaning. Declined Pressures are good but coil is dirty. High side is hire than should be
Annual maintenance on Ruud air conditioner
Performing maintenance on a 2013 Goodman air conditioner.
Customer has an old trane unit that is leaking refrigerant. Proposed professional installation of American standard air condition and 80% furnace