From the first phone call with Joseph to the install I can’t say enough. Everything was so smooth and fast.
Alex was a very experienced and knowledgeable technician. Excellent customer service
We were not able to be at our house while the new AC was installed. Joseph did a great job communicating and sending pictures of the installation. He went above and beyond and returned the next day to make sure everything was working properly.
fast and friendly service
Great service, very friendly. I Will for sure call Joseph for next project
He was knowledgeable, on time and professional
Full inspection of system and discovered unit had no freon and has a leak at the condenser or indoor coil, furnace & blower performing within manufacturer specifications.
Installed Daikin 3.5 Ton Condenser & Evaporator Coil with drain pan, float switch, condenser pad, flushed line set, pulled vacuum, insulated copper & pvc & replaced 2 foot of primary & secondary drain lines.
Ac Repair: primary drain line is clogged, recommend cutting and clearing drain line. Cleared drain with nitrogen. Installed float switch on secondary drain pan. cut the drain line, blow through the primary drain line with nitrogen, then repair the drain line back to normal.
Ac Repair: low voltage break in unit 16 control wire, replaced low voltage wire and system is operstong normally at this time.
Diagnosed both 2 Ton Lennox & 3 Ton Lennox Furnaces and found blower motors were no longer working, ordered parts and will perform installation of 2 new blower motors.
Installation: installing new ecobee thermostat. Need to unwire the existing thermostat and EIM form unit and wire all 5 wires into furnace. Thermostat is installed and operating normally at this time. Talked about comfort club membership, customer is not interested at this time.
Ac Repair: found break in the low voltage wire for unit 15, recommend replacing low voltage wire on unit 15. Replaced wire for unit 15 and found that unit 15 and 16 were in reverse order of the notation. Found the correct wires for unit 15 and attached. System is operating normally at this time.
Maintenance: signing up for maintenance on four units.
Replace the heat kit under manufacturer warranty.
Maintenance: Bronze Comfort club memberships for 3 units for one year. Semi-annual system maintenance and filter change, supplied by owner. After hours service, and 10% discount on repair labor. Performed maintenance on all three units.
Maintenanced both systems and found both units a little low on freon, recognize they might not perform as well during the summer.
Maintenance: finished replacing filters and diagnosing the QC office split system.
Maintenance: performed system maintenances and replaced filters. Replaced filters on four new units.
Installed 2 Coleman 3 Ton 2 stage gas systems with wifi thermostat, drain pan, drain lines, gas flex, flue pipe, supply & return plenums, condenser pad & 10 Year parts/ 10 Year Labor.
Performed maintenance and found system low on Freon, charged with 2lbs of freon and temperature Split was 18 degrees and pressures were within manufacturer levels.