Conner was courteous, on time and explained the work he did on the service call. He made sure all my questions were answered.
We have been with Stuart Pro Air for many years. The service is great.
Very thorough, nice customer service, Respectful and courteous
Very prompt and professional
We have used Stuart Pro Air for many years. Their technicians have always been consistently polite, on time and offered great service. Today was business as usual, very pleased!
We have been with Stuart Pro for many years. Appreciate the service.
Completed a heat maintenance for a goodman furnace, found a really dirty media filter, other than the filter there are no issues at this time.
Completed a heat maintenance for two goodman furnaces, found both units with dirty flame sensors, so I cleaned them up and they work good as new.
Completed a complimentary heat maintenance for two Trane furnaces, found both systems gas pressure to be higher than normal, reduced them to the most efficient setting.
Completed a heat maintenance for a zoned Trane heat pump. No issues with this system.
Completed a heat maintenance for two 17 seer Trane heat pumps, found a dirt filter for the main level and found no current issues with the systems.
Performed a one system duck cleaning on a furnace split system. Covered up all vents to increase vacuum pull throughout all vents, covered filter and coil so both would not get dirty, and cleaned all duct runs. Turned unit on after finishing to insure it started up properly, and left.
Upstairs was blowing hot air when not being called for. Found one of the zone dampers for upstairs not wired at all, wired damper to zone board and now zones are opening and closing properly.
Completed a heat maintenance for a Trane heat pump, found no issues with the system after no service for 4 years.
Addressed homeowners airflow concerns and made sure the home was up with code.
Addressed homeowners concerns and airflow issues.
Homeowner had airflow issues to her master closet, showed homeowner how to adjust manual damper that had been installed but was closed.
Completed a heat maintenance for two Trane furnaces, found a stuck damper for the basement zone. Got it to open and it is working properly at this time.
Completed a heat maintenance for two Lennox furnaces, found a blower capacitor reading lower than what I like to see, so I recommended replacing it and the homeowner agreed.
We replaced a Trane furnace under warranty.