Our heat was not working and within 30 minutes Paul had it working and clearly explained what cause the failure. I am glad that we can rely on him to care for our heating and air conditioning issues.
David was awesome and was able to fix a problem quickly due to his technical expertise and experience. Thank you!
Very informative, and excellent service. The technician was fantastic. Thanks
Tech was great
Replaced bypass damper in metal bypass and set to .8 inwc.
Performed maintenance on a package unit
Replaced contactor and verified operation.
Service call. Fan spinning the opposite way and stopping.
Performed maintenance. Client replaced filter. Verified proper Delta T. Verified heat kit works. Tested safety switches. Electrical connections are secure. Amp draws are good. Installed UV light. Cleared drain line. Capacitor is testing within proper range. Cleaned coils. Unit and components are operating properly within manufacturers specs with no issues at this time.
Return for parts
Completed tune up.
Performed tuneup for cool club members on split system heat pump. 2 zones.
Upon my arrival I found the downstairs system operating as it should at this time. Educated customer on how the system operates winning defrost. System is operating as it should at this time.
Performed maintenance. Replaced filters. Verified proper Delta T. Verified heat kit works. Electrical connections are secure. Amp draws are good. Cleared drain line. Capacitor is testing within proper range. Unit and components are operating properly within manufacturers specs with no issues at this time.
Completed tune up
Upon my arrival I found the package heat pump down because of a faulty reversing valve. Customer states he is going to have another opinion. Iâ€™m creating an estimate for repair.
Corrected install wire up and adjusted the manual dampers on the duct system to get the airflow issues resolved. Collected payment for install
Performed second tune up on three systems replaced contactor on second floor outside unit