Tech came out on emergency call we needed a new board and blower motor. Order them next day. He made sure the house was cooling.
Great Customer Service
The two guys that did the job were great.They were very polite and very knowledgeable. awesome job.
David was able to take care of my problem in a very short period of time.
Chris was congenial, straight to the point, efficient, and very good at explaining( and fixing)!
Found unit barely frozen found pressures low and the Schroeder valve failed on suction line replaced under part warranty charged for refrigerant.
Arrived to find bad stat not sending a call to G. Replaced stat and checked operation.
One of the two system was working the one up stairs had a loose terminal lug for reversing valve causing heat to cycle on instead of cool.
No cool and fan runs non stop.
Outdoor unit condenser coil needs cleaned, estimate is in the system. They will call and schedule.
Ac not blowing
Not keeping temp
TSTAT is reading A201 for a tripped float switch
Ac not cooling properly
Performed maintenance. Client replaced filter. Verified proper Delta T. Tested safety switches. Electrical connections are secure. Amp draws are good. Cleared drain line. Capacitor is testing within proper range. Refrigerant pressures are good. Cleaned coils. Unit and components are operating properly within manufacturers specs with no issues at this time.
Compleated maintenance on a Goodman split system heat pump. Cleaned all components sucked out drain line changed filters and educated customer on hard start kit. Unit saved 40A on start up. Is going to think about next time.all systematic components are functioning properly at this time.
Strapped up drain where duct work was pushing down drain line changing pitch ran vacuum on drainline just water no loose debris. Drain is draining put a video in service titan. Covered by warranty.
ANNUAL CLEAN AND SERVICE. SILVER