Performed a maintenance check on customers Air Conditioner. Unit is now cleaned and working properly.
Check/remove Supco Surge Protector.
Preventative maintenance check and cleaning on furnace.
Blower motor in Armstrong furnace not kicking in properly.
New AC heat pump installed, tested, and inspected.
No AC call, current unit is not reaching temperature. Pipes frozen up, water moisture around base of unit as pipes thawed. Owner thought was leaking but just condensation from pipe. Too low on refrigerant caused AC to overwork and freeze up. Unit is 15 years old, informed customer about r22 and it's costs. Created Estimate for new unit, as it is more cost effective to get a newer unit that runs off 410a refrigerant.
Clean and check
Hvac repair. Service call on a carrier unit. replacing contractor
Hvac Maintenance. clean and check, changing filters on trane units. enhances units life.
Hvac Repair. service call on an A/c
Hvac Repair. installing new blower motor in a carrier unit
Hvac repair. installing new glow plug in a carrier furnace
Hvac maintenance. Clean & check, changing filters on lennox units
Hvac Repair. installing new glow plug in a trane unit