Technician was courteous and friendly; thorough inspection.
Always good work
Wonderful service just like always!
Very profiecient and knowledgeable nice person
Kyle provided excellent service in scheduling the appointment. Shawn was professional and did superior work. Charlie was great. I highly recommend this place.
Thanks to Pete for a great visit. Very pleased with your service. Answered all the questions we needed to know.
Great service experience!
2021 PCSA PREPAID AC Check Up
2021 PCSA a/c check up prepaid Downstairs system needed 1 lb of R-22. Everything else was clean and checked out well. Both systems are operating normally.
Complaint no a/c .topped off charge by superheat
2021 PCSA PREPAID Spring Check Up Replaced 60 amp ah breaker and added 1.5 pounds of r22 Other checks good
PCSA 2021 AC Check Up Renewal . Washed unit unit cks. Ok.
PCSA 2021 AC Check Up 2 Systems Renewal . Old system will need contactor & cap. Soon. Check on premier one rebuild kits
2021 PCSA a/c check up 2 system prepaid Ptac capacitor good amps good delta t good filter cleaned coil brushed off
2021 PCSA RENEWAL Cooling Equipment Maintenance Everything was clean and checked out well. System is operating normally at this time.
2021 AC Check Up Renewal . New filter washed condenser removed leafs from bottom unit in good order
Quote for 16 SEER 5 ton York 5 stage heat pump and York electric furnace
Quote for 2 1/2 Ton 17 SEER York heat pump and York electric furnace
Complaint: AC Not Cooling Properly No ac found first stage compressor with an open winding, cooled compressor, winding opened up immediately. Hooked up second stage compressor, would like a quote on a new system. Pete coming by tomorrow to price
All systems check good in cooling still need a 24x24x2 for system #4 win air was out when I checked. All filter sizes recorded in folder
Complaint no a/c upstairs unit .no refrigerant in unit needs free est.
2021 PCSA a/c 2 system check up renewal Everything was clean and checked out well. Systems are operating normally at this time.