Really like Layne and his team, they worked miracles for us and got the yard back! Service was awesome, but Andy's prices for parts were a bit high IMO.
Layne came and fixed an ancient irrigation system. He carefully explained each step and gave the reasons and explanations for each repair. I am truly amazed that good service still exists in our modern world.
My husband and I are in our 80's. Kirby exhibited admirable patience in dealing with us. He and Ignacio were well qualified with all of the work. In fact, we appreciate all the advice, along with the adjustments we requested in their work. Kirby taught us how to use the new control box. His advice to get a better box was taken, and we are glad he urged us to do so.
My Tech was I formative and explained everything well. Very friendly and knowledgeable
Albert was very knowledgeable and fixed all the issues with our sprinklers and water pressure. He was prompt and courteous! Highly recommend!
Best service from a contractor ever! Very professional!
Layne & his crew far exceeded expectations!
The service contract is a lifesaver. Albert always takes great care of our watering system.
My house was hit by lightning. Called Andy's Sprinklers (I've used them before), they were out there that day. The sensor for the old control panel was what the lightning hit, blew it off the wall. Destroyed several of the sprinkler solenoids, lost probably over a thousand gallons of water (not an exageration). Noe and his partner fixed everything, kept me posted as to what they were doing, and did a fantastic job. Andy's Sprinklers and Noe are Highly Recommended.
Full system check couple minor
Investigating drainage issues in San Antonio 78240
Full system system check couple minor
Customer called for a broken head in the backyard. We checked entire system and found 1 other head up front that would not stay set. We also made adjustments throughout system to make sure all grass was getting covered.
We checked the system and found a pipe break and a couple broken heads. We also changed a few stopped up nozzles.
Customer called for zone 1 not working. While checking system we found zone 1 was showing an error. We found valve and determined valve was going bad. We changed the valve then checked system and replaced 1 head.
Mr. Garcia called for 3 out of the 5 zones not working. When we arrived we tested wiring and found everything was okay. When testing system we found zones 2, 4 and 5 not coming on. When we located valves we found we had 3 bad valves and replaced them. We tested system again once work was completed and changed out a few nozzles.
Customer called because 3 of the 6 zones were not working. When we arrived we found zone 1, 3 and 4 had bad valves. We located all the valves and replaced. Zones 3 and 4 valves were under the deck so we had to pull the deck boards up to get to the valves. Once they were replaced we found we also had a wire issue and ended up running a 3 strand wire around the deck and under to the valves. We then checked system and replaced a rotor and a few heads. We also repaired a few pipe breaks.
Customer called for system check. When we arrived we checked system and found a number of heads leaking along with pipe breaks. We also found zone 5 had a bad valve that we had to replace. After work was completed we tested system again for any leaks.
Customer called for system check. He mentioned he had a zone stuck on when they turned the system off. We turned on power to pump and found zone 7 was stuck on. We replaced valve then checked system. We found multiple rotors on every zone either leaking or sticking. We also found all 12” heads on zone 10 sticking and leaking. We replaced all leaking heads and checked system a few times over to make sure nothing else was leaking.
Completed general maintenance system check. Replaced several sprayheads and nozzles for more efficient coverage throughout the system.
Replacing a controller and a valve.
Doing a small overhaul on a system.
Customer called for zone 5 not working. When we arrived we found zone 5 not working because of a cut wire. During system check we found a few heads leaking along with a couple pipe breaks. We started tracing zone 5 wire and found a cut wire underneath a small tree. After repairing wire we found zone 5 valve was also bad. We changed valve and repaired leaks then checked system again.
Completed general maintenance system check. Installed drip valves and repaired drip lines.