Was able to come earlier than expected. Diagnosed the problem quickly, left to get the parts needed, and came back to finish the job.
I had a technician come look at my HVAC unit. I was happy with the services provided.
Pleasure to do business with RA Nichols Plumbing and Heating. Dominic has been my technician each time and tacks care of the problems in a timely manor and explains it in terms I understand.
He came right away, solved the problem fast, very friendly.
Dillon did a great job, fixed problem, very nice young man.
I am impressed with the excellent, fast service that I received. Dominic is extremely personable and explained the problem clearly, showing me the part that needed to be replaced. If I should need any service in the future, I will always call your company and I will recommend RA Nichols to all of my friends. Thank You
Dylan was professional and did a great job. He can on time and finished the job as estimated. He provided great suggestions and options with details of the price for the job. Well done!
Very professional service. Will highly recommend.
Angle stops + descale
1st floor toilet needs new handle. 3rd floor, one toilet (room towards front of unit) needed a new flapper and fill valve given explanation of customers complaint and techs observations of operation. Which was rebuilt on this service call. Toilet is properly functioning without leaks or issues. *awaiting approval of landlord The other toilet (3rd floor back of unit) recommended rebuild due to fill valve showing signs of leaking . Basement toilet recommend rebuild as well due to fill valve showing signs of leaking and not properly shutting on and off. Tech observed all toilets are American standard and similar in age and models. It is recommended all toilets be rebuilt given age , wear and tear of normal use and signs of deterioration of parts.
Tech cut out customer repair that he had made with shark bite fittings and replaced with pressed ball valve. Water was turned back on without leaks present. Shower valve was disassembled to find that leak was coming from faulty gaskets on the diverted lever. Lever was removed and old gaskets where removed and new ones installed in place. Shower valve was reassembled and is functioning as it should with no leaks are present.
Replace electrical component transformer with new. Transformer not sending voltage to board so to further diagnose need to replace transformer.
new plastic handle insert and for moen 3 way transfer valve & replace
Customer explained to each the hose bib had broke and wanted to replace it and bring the shut off valve upstairs as opposed to having it in the crawl space. Tech cut out and remove old hose bib and valve, and capped old line. Master bath lav sink was used to tie in new shit off valve before pip went back into crawl space for new FF hose bib to exit back out of pre existing hole in place of the old one. No leaks are present at this time, and insulation was put back in its place.
Tech removed old Delta faucet, however upon removal of old faucet old shut off valves were leaking, tech cut out hot water side and replaced with a ball valve. However cold water side had two valves so tech cut out old gate valve and due to interference with new faucet hose line, a ball valve was not installed. New delta warranty supplied faucet from customer was installed, no leaks or malfunctions are present at this time. **** Mail copy of invoice to customer
Installed customer supplied wine cellar unit. Remove old equipment as well.
Going ahead with blower motor replacement taking off price for repair
Repair toilet shut off
Replaced batteries on thermostat
Faucet making noise