We live out of state and needed work done during a specific time we would be visiting our property. Cameron from Rocksteady plumbing was very accommodating and made sure everything was ready to take care of our issue during the short period we were here. He took the time to explain everything so we would interest and what was needed, what they would do and how to prevent it in the future.
Very knowledgeable! Great work! Will use company again! Thank you!
Mainline stoppage downstairs bathroom flooded. Ran snake ti clear line. In San Miguel.
Installing two new Mirabelle tub / shower cartridges. In San Miguel.
Inspected and repaired a failed well pump motor that had a faulty capacitor in San Miguel.
Fix the leak in a water softener. The head was loose so we pulled it apart regreased it and put it back together. Everything just good.
Removed shark bites behind vanity and replaced in pex.
Arrived to the job to find no air code on a Noritz tankless water heater. Went through the hot water heater with Tech Support and found out the mixing valve is bad. This water heater is under warranty.
Found a 3” sewer drain that had broken straps. It was completely back graded and laying in the dirt under the unit. we had to run a mainline cable in order to break up call the solids so that we can pick the pipe up and hang it.
Found a rinnai tankless water heater that was not producing hot water to a bathroom. After taking a look around the jobsite, we found a shower valve that was roughed in with the stops open so it was creating a crossover.. after figuring that out and turning the research pump on on the water heater everything tested great.
This is an install of a customer supplied Moen cartridge.
New pop up assembly.
Leaking Garbage Disposal under kitchen sink, Replacement of moen shower trim, tubular waste rebuilds underneath kitchen sink, and lav sink.
Performed a backflow preventer assembly inspection on a Wilkins 450 DCDA assembly in San Miguel.
Performed a backflow preventer test of a Wilkins 975xl RP assembly in San Miguel.
Performed a backflow preventer test of a Febco 825Y RP assembly in San Miguel.
Replace service valve hose bib