Reroute all 3/4 gas, hot and cold incoming out to exterior up to 8 ft away for tankless installation Mount tankless on exterior of home Install flush valve kit Install tankless unit with internal recirculation line Install recirculation line up to existing output Prescribe tankless service up to 6 months from install date Plumbing estimate does not include any carpentry or drywall putback
Leak Detection in home
Arrived at 1701 Mojave circle, Corona ,Ca. Performed leak detection at home did a Pressure test in front of home,Failed. Came into home with leak detector loudest reading was on 1/2” hot line under kitchen sink cut open to locate manifold.once located found 1/2” burst hot water line above ground repaired line water back on with a pressure test performed at the end, Holding Pressure.
Customer softener wasn’t discharge water from the brine tank. Removed all salt and build. Made sure float was free and clean with debris. Filled back up the brine tank with fresh salt new water. Regen cycle will go off at 2pm. At 8pm please hold down the regen button on the unit to start another regen cycle after that cycle your system will be back to normal.
1/2 cold water at the kitchen was the loudest fixture. Didn’t see any sign of water damage.
Performed free leak detection in home at 1126 silver eagle circle, Corona, Ca. Customer has a double slab leak one on the hot side goin from guest bath to master bathroom. Secondary leak from toilet to master bathroom lavatory sink. Third slab leak recommend repipe
Needs to figure out when when can come back out.
Performed leak detection at 16225 Sally ln, riverside Ca. Upon arrival customer complained about hot tiles. Performed pressure test and immediately failed. Went to location of hot tiles in kitchen used leak detector go high reading at water heater and kitchen performed cut and cap on manifold. Upon opening behind water heater noticed water coming out of slab cut one branch and notice water not holding in pipe cut and cap was performed. Pressure test failed again. Cut and cap second middle line performed pressure test and hold. 2 hot water lines affect areas are hot to master and guest bathroom, and kitchen sink. Recommend a pex push for kitchen sink and reroute for master and guest bathroom.
This price is valid if the have a accessible clean out in front yard.
Change out gas valve
Water heater estimate
Customer Frank requested repipe home up to two bathrooms due to integrity of previous plumber’s work. Crossed pipes, touching pipe, no strapping etc. Repipe all water lines full resupply up to all existing fixtures within 2 bathroom home- single story Install all quarter turn new angle stops with supply lines for each fixture. Installing of 3/4 pressure reducing valve Install emergency water shut off Install hot water heater ball valve Install two shower valves without access Install two hose bibs without access Plumbing estimate does not include carpentry repairs Plumbing estimate does not include water heater, any fixtures, custom trim/escutcheons, or irrigation. Plumbing estimate will include a partial discount for PLUMBING services sold may 16, 2023.
Performed leak detection at 1271 Dover circle performed pressure test. FAILED. Seen buckling floors throughout the house. Performed hearing test on kitchen It was 1/2 hot water line is comprised that rolled from the water kitchen to water heater.