Commercial Ice Maker Installation. A hospitality facility needed a new ice maker for their high-demand ice requirements. We positioned the ice maker, connected the water and drain lines, and fine-tuned the ice production settings. Thorough testing confirmed efficient ice production, enhancing the facility's service.
Arrived on, 09/09/23- Steve- Call Out- Found unit to have tstat set to cooling and unit at 80 degrees. Went to roof and found compressor extremely hot and condennsing fan motor to hot to touch. Tried to turn u it on and tested fan motor. Fan did not spin freely. Replaced condensing fan motor and then had to cool compressor to turn back on. Turned u it on and tested. Unit is in operation at this time.
Arrived on, 08/15/3- Matt- Cabinet was at 46 degrees when I arrived and the condenser fan was running but the compressor was hot and went off on overload. The condenser coil was clean so I put gauges on to check pressures. Pressures were low so I leak checked the unit and found the access valve on the compressor suction process tube was leaking. I replaced the access valve, changed the filter drier and pulled a vacuum on the system. I added refrigerant and waited for the unit to come down to temp and with the thermostat set at 4 it cycled off at 35 degrees. Unit is now cooling properly.
Commercial Charbroiler Installation. Installing a commercial charbroiler for a commercial client, we ensured proper ventilation, gas connection, and heat distribution. Thorough tests guaranteed even cooking results.
Commercial Food Warmer Repair. The warming cabinet's temperature was fluctuating, impacting food quality. Our adept repairman meticulously examined the unit and determined a malfunctioning heating element as the root cause. The faulty element was expertly replaced, ensuring consistency and even warming throughout the cabinet.
Commercial Microwave Repair. A commercial microwave's timer malfunctioned, causing confusion in cooking durations. Our technician promptly replaced the timer unit, restoring precise cooking times for reheating and food preparation.
Commercial Dishwasher Repair Service near W Main St. We were contacted by a commercial kitchen that had a malfunctioning dishwasher, which posed a great risk to the business's operations. We promptly arrived at their location and proceeded to examine the dishwasher to determine the cause of the performance issues. The examination uncovered the source of the problem to be a faulty water pump. I replaced the water pump to get the dishwasher back up and running quickly, ensuring smooth operations for the client. The client was appreciative of the quick response time and the efficiency of the repairs.
Commercial Kitchen Repair Service near W Locust St. Upon receiving a call from a commercial client regarding their malfunctioning commercial beer cooler, we promptly dispatched a technician for repairs. I swiftly arrived at the client's place of business and proceeded to diagnose the issue with their appliance. Through careful investigation, I identified the frozen temperature control unit as the underlying cause. To resolve the problem, I replaced the temperature control unit and conducted thorough testing to ensure it could maintain the required temperature accurately. The client expressed immense relief upon having a fully functional cooler for their business operations!
Commercial Kitchen Repair Service near E Allen St. When a commercial client was experiencing difficulties with their commercial convection oven, they contacted us for repairs. I quickly arrived at the place of business and assessed the issue with the client’s convection oven. The investigation led to the source of the problem being the appliance’s internal fan. The fan was inoperable and required replacing, so I replaced the internal fan to bring it back to working order. I tested the oven to ensure proper circulation and it was working well again upon my departure. The client was relieved to have a working oven for their business operations!
Arrived at location on 10/27/22 - Checked out unit and found that the main water fitting that goes into the three way valve was leaking. Pulled unit apart and resealed all the fittings. Reassembled and checked operation by running unit. Found nothing leaking at this time.
Arrived at location on 8/1/22 - -Checked out unit and found that pilots were out so relit them and let heat up. Checked the temps and adjusted them. Checked operation, ok. Let cycle on and off, ok.
Arrived at location on 6/3/22 - Customer was having to issue with coffee brewer tripping gfi outlet. Had customer brew pot of coffee no issues. I asked if it gets moisture back where unit sits and manager said it does. Removed bottom pot warmer and found wires to element showed that they were wet at one time. Customer gave me a sheet tray and I placed coffee brewer and grinder on top of it to help keep moisture away from warmer. All ok.
Arrived at location on 1/11/22 - Checked out unit and found the water is by passing water valve and is leaking around the gauge. Will order and return. Returned to location on 1/13/22 - Arrived on site and spoke to mod. Verified that parts was correct and began to remove listed parts. After installing I checked for leaks and run dishes cycle multiple times. Rinse cycle had 20 psi. Unit is working at this time.
Arrived at location on 8/27/21 - Checked the unit and found out that the elements on ohm were OL. I called manufacture and spoke to Mark and he confirmed that the unit parts were out of stock and were not made anymore. The unit is over 16 years old. Customer would like a quote for a new unit.
Arrived at location on 7/14/21 - Checked out unit and found that the start button was working fine on arrival. Per customer the start button would stick in and not come back out. Tried starting and stopping several times and worked every time will obtain start and stop button and return. Returned to location on 7/23/21 - Returned with parts. Removed old stop and start switch and installed new stop and start switch. Checked operation, ok.