The service Jason provided was excellent!! He explained some things about our system to help us understand better. He was very professional & certainly seemed to have complete understanding of how our systems worked. I would welcome him back again to provide ongoing service. You should be proud of the way he conducts himself & if the knowledge he possesses—was most impressed!!
AC performance tuneup times two systems. Supply and change out 116Ã—25 times for filter. Also 120Ã—25 times for filter inspect mowers, evaporators and ductwork. Checked thermostat for proper operations. Verified primary drains are clear at this time. Check outdoor units. Refrigerant levels good in both units. System on the east side of the home is 17 years old. Recommendation is to change out. Wash both condenser coilâ€˜s. Checked all capacitors and contactors. System is cooling properly at this time.
Perform 2 system maintenance clean both condenser changed downstairs filter and upstairs filter should be change as well I let Charles know. System specs are on the maintenance forms. Recommend replacing the grey flex ductwork due to its age and not being hung properly. Both systems are cooling at this moment.
Arrived to find system not running outside and not getting 24v. Went to furnace and 24v wire was connected to only one leg of the ac. System needed to be hooked to y and ylo. Once it was connected system still didn't run so I bypassed the rectifier and got them running but only in first stage. When Compressor starts and stops you can hear there's a problem. Need to double check on how to proceed and given the time I bypassed the rectifier to let system run in first stage to keep cooling. The liquid line has been crossed threaded so only low pressure was checked but within range. Can confirm ac is running but compressor has further issues that need to be addressed asap.
Walkthrough on 2 system install. Both systems installed properly and level. All duct connections properly sealed except for one. I mastic sealed it. Condensers properly wired and level. When I arrived Mrs. Wickstrom informed me of a concern she has had for a while. She stated that â€œblack stuffâ€ was coming out of the registers. I informed her that it was bacteria growth due to the age of the ducts and that they were not sealed. This allows hot and cold air to mix which creates moisture in the ducts, which eventually grows bacteria. The register in the upstairs bedroom with the baby crib is definitely the most concerning. Upon inspection I noticed that the boots were Internally insulated. They are rusted to the point that the tabs on the start collars have fallen off and there are large amounts of bacteria growth. Mrs.Wickstrom stated both upstairs bedrooms are always cold/hot (cold in winter hot in summer). Both upstairs bedrooms duct sizes could be increased. I inspected the ductwo
Performed heating maintenance, cleaned flame sensor, treated drain lines, changed filters, inspected blower compartment, and checked all components to be operating within manufacturers specifications. Heating form filled out and all recommendations listed on it.
Replaced complete upstairs system with new Trane 3T XV20i - Trane 10 yr parts warranty - Dealer 5 yr labor warranty - 5th year maintenance on new equipment
Replaced complete downstairs system with new Trane 5T XV20i - Trane 10 yr parts warranty - Dealer 5 yr labor warranty - 5th year maintenance on new equipment
Downstairs system has 10ppm of carbon monoxide. Upstairs system has 16 ppm of carbon monoxide. Due to health and safety concerns I have disable the heat function on these furnaces until the customer has resolved the carbon monoxide issue. The ductwork is old grey flex with duct board mixing boxes and it is all starting to break down. The complete downstairs system is from 1999 and the upstairs furnace is the same age with the cooling side being from 2010. I would recommend replacing these systems due to age and I would recommend replacing the ductwork for a higher efficiency.
Arrived to find gas valve turned off. It was turned on and heat is running. Maintenance was done on both systems as well. Airflow was adjusted on the down stairs unit and multiple vents were switched to blow in the correct direction. Senors cleaned, amps checked, pressures all.checked out. May need to adjust the airflow again please call !!Jason if issues arise.
replaced complete ductwork on both systems
Replaced the disconnect.
Post install walkthrough. System sealed and hung properly. Had to fix the pvc piping because the plumber capped drain from coil to sink. Customer would also like warranty information and install manual for condenser.
No cool. Upon arrival condenser was not running. Diagnosed bad breaker in disconnect. Replaced breaker for now since its is raining but will need to come back since line voltage side of disconnect is burnt up and will replace whole disconnect.