Jason spent time looking at air flow and adjusting my unit and vents to maximize efficiency. He also explained things well so that I understood what the issues snd end goal were.
Cole was very thorough and explained things as he went along
left quote for duct cleaning
Ac checkup on unit. Inside unit checked along with blower and coil. Condenser checked, air speed checked, fllter checked. Condenser was rinsed and freon was balanced. Compressor Amps, contactor and capacitor all.with range at this time. Suggestions are to fix the drain lines and upgrade the thermostat to one that tracks humidity which I'll an estimate for in the invoice.
All systems working properly in heat mode at this time. Recommended surge protection on lower level system since it does not have any. I informed Mr. Coates that the upper level upstairs system is still eligible for an extended labor warranty. I also informed him about the nexus smart home equipment that we offer that integrates with thermostat app.
System working properly in heat mode at this time. Found a rodent laid acrossed the capacitor. Fixed wiring and replaced capacitor. The hard start kit has failed and I would recommend replacing. The compressor is pulling high LRA. Replacing the hard start kit would give the compressor more life especially since its a heat pump.
Performing a 3 Systems Heat Tune in Euless
Cleaning and maintaining Trane air conditioner in Euless
Cleaning and maintaining Trane heat pump system in Euless