Jason noted a few inefficiencies. Very professional. Appreciate his attention to detail.
Joel came for seasonal check and discovered a coil leak, arranged to replace coil that’s under warranty. Very thorough, and glad to discover now instead of July or August.
Had a problem with my AC, still under warranty. AC Pros came out immediately, and though the problem was difficult to diagnose, they stayed on it and found the cause, and completed the fix. I’ve been very pleased with their service.
Cole did an efficient job on the service check on our HVAC. Nice guy!
Damon got us fixed from a surge problem due to constant power failures during a storm a few weeks ago. Got a new thermostat that has an IPhone app.
Excellent service. Very personable.
Install techs awesome. Very professional and tenacious. Worked long into the night to finish the job.
It’s nice when you can build a relationship with a person and they get to know your home as well We have been customers for almost 20 years and Jairo has been one of the best!
AC performance tuneup times one system. System as a zone with an upstairs bedroom. System does not have a bypass damper. Which causes the upstairs to blow away too hard when it is the only zone calling. Treated drain lines with white vinegar. Checked thermostats for proper operations. Check outdoor unit. Refrigerant level is good at this time. Test capacitor and contactor. System is cooling properly at this time. System is 15 years old and is our 22. Recommendation is changing complete system
Customer wants to reschedule for a day itâ€™s warmer and would like the correct grills installed. 2 returns and a supply
AC performance tune up times one system. Change the oil filter client Supply. Verified primary drain is clear. Inspect blower, evaporator. Evaporator is leaking. Check outdoor unit. Refrigerant level was extremely low. Added nine pounds of AZ 22 system. Office will call and schedule if the 13th or sooner that we can install the evaporator coil wash condenser coil. System is cooling properly at this time.
Return today to diagnose system. Found the outdoor eev not responding. I reset the board on the heat pump outside has system started operating properly. I ran first and second stage cool and Heat. System is operating at manufacturer specs at this time. Also added 6 oz of supco 88 additive from Trane.
Leak search on heat pump system. Pump down condenser and put 375 PSI on system for 1.5 hours. Did not drop any at all within that time. Check outdoor unit. Use bubbles to try to locate leak. Could not find leak. When I started the unit backup it ran perfect and the AC mode. Upon starting the Heat the circuit board outside gave me an error code flash 7. Which stated that the valve was responding but system was not operating properly. I put EEV through test and it said it was opening and closing just fine. I will need to get with Trane tech support to find out what revolutions can be taken.
Heat performance tune up times one system. In fact blower, evaporator and ductwork. Test all safety features. Tightened on wire connection. Located two broken spades on the heat strip relay. Repair those and they are operating properly now. Test if he tries. 40 degrees temperature rise. Check outdoor unit. Refrigerant level good at this time. Test capacitor ,contactor and defrost cycle. Wash condenser coil. System operating at manufacturer specs at this time.
Both systems working properly in heat mode at this time. I had noticed both furnaces are new, but both condensers and evaporator coils are 12 years old and use R-22 refrigerant. I let Mr. winters know that R-22 equipment is no longer in production per EPA and that as of January 1st all equipment manufacturers are raising their equipment costs.
Changed out heat strips but system still has a blockage and trane needs to get involved.
Arrived to find system wired wrong along with a leak that we still can't find. Will return with correct heat strips and nitrogen to find the leak. Wiring issue was resolved
System functioning properly in heat mode at this time.
Evaporator temperature sensor and Gas temperature sensor not making good contract to coil. Resecured both and reset system. Heat pump is operating at MFG specs at th
Arrived to find unit encountering some issues. Will be talking with trane to set to come back tomorrow between 1-5. Grills needed are sidewalls and one way curved blades. Make sure you measure the back of the grill and not the face of it when ordering them.
System working properly in heat mode at this time.
Pump system down and changed out defective TXV. Pressurized and if I created system to 700 micron. Verified charge is correct. System has a 10Â° subcool. Turn system off and let pressures equalize. Turned on heat. System is operating at manufacturer specs at this time. I am I am not charging Bill at this time because I feel like we are the blame for messing up the TXV. Bill stated that before the compressor stopped running it was Cooling. It's possible that too much set from not purging closed the TXV.