Very nice and helpful.
Response from AC Pros:
Brad, Thank You for the 5 star! -Sincerely, Russ and Laura Teager AC Pros
Perform 2 system maintence clean condenser coils specs are on maintence forms both system currently cooling properly
Completed a/c tune up, washed condenser coils, flushed out drains lines. Refrigerant levels are good, blowers and compressors amps are in range, run capacitors were good.
Heat performance tune up times two systems. Inspect blowers, evaporators and ductwork. Test all safety features High limits and roll outs. Tightened all wire connections. Check heat exchanger for cracks, found none. No carbon monoxide or gas leak detected in home. Test thermostats for proper operations. Systems operating at manufacturer specs at this time.
Arrived to find hsi bad but getting voltage from the board. Furnace is over 2 decade old and replacement is suggested. Can confirm heat is running at this time.
No cool. Upon arrival blower was blowing but condenser wasnt on. Found a tripped Float switch. I cleared the drain and system started cooling. Also installed two 16x25x1 filters
No cool. Upon arrival found a tripped Float switch. Cleared the drain and system came back on. Recommended repiping the drains for the two systems in the attic to have better pitch so they drain better. The primary drains on both systems tie together.
Repairing Honeywell Zone dampers in Highland Village
Estimate on replacing air conditioning heating system in Highland Village!
Doing walk thru on 2 newly installed Trane units in Highland Village
Performing a 2 systems A.C Maintenance in Highland Village
Trane complete install in highland village
Installing trane system
Doing repairs to the Air Conditioning in Highland Village
Doing a 2 systems heat tune up in Highland Village