Very good company to do business with. Very fair and they do excellent work.
Installed 1/3 220 volt 1075rpm blower motor for upstairs condenser.
Completed diagnosis, condenser fan is faulty. Need 1/3 to 1/6 :-P 1075 rpm 220volt fan motor. And give price.
Completed A/C Maintenance check out. Added two hard start kit to both systems. Run capacitors, compressors, fan and blower motor are good. Flushed drains. Also refrigerant levels were good.
System working properly in heat mode at this time. 20x25x4 filter is dirty and needs to be replaced
AC performance tune up times one system. Verify primary drain is clear at this time. Filters been changed recently. Test thermostat for proper operations updated thermostat to latest Trane version. Check outdoor unit. Refrigerant level good at this time. Test capacitor and contactor. Watched coil on condenser thoroughly. There was a whole lot of grass clippings embedded in the coil. System operating at manufacturer specs at this time.
Providing an estimate to replace air conditioning in Little Elm
Installed Trane 824 Thermostat and Nexia Camera
Performing a 1 system heat tune in Little Elm