As always, great service.
I asked for the unit to be checked to figure out why condensation was happening and why it was so humid. I was told the coolant was good and there was nothing else they could do.
AC performance tuneup times three systems. Client changes on filters. Inspect blowers, evaporators and ductwork. All three systems have good temperature drops. Ran water through drains. Wash condenser coils. Systems are operating at manufacture specs at this time.
Upon arrival checked with customer the following are my findings Upstairs and downstairs in the main house are working properly at this time they're on you're 2 of their life have concerns about duckwork please see pictures attached going to reach out to manager and see if we can remediate some of the issues we'll get back to customer with solution please see pictures attached 3rd unit is working however capacitor is showing signs of adverse wear
Installed new evaporator door. Noticed that there is a aftermarket UV light in direct contact with the metal side of the evaporator door. It should not have any bearing on the plastic but for some reason it is. The breaker panel is also deteriorating. The UV light is called air health. For some reason it is deteriorating the poly cabinet of this air handler.
I replaced the Furnace Control Board for the 2nd floor. I installed Surge Protector’s on both Systems. I rechecked operation of all equipment after repairs were made. Everything appears to be functioning as expected. At this time.
Neither System is working correctly. I noticed significant Voltage spikes 218v-238v. This can and will cause communication issues and electronics damage. The Downstairs System is coming on intermittently. The Customer states this is new! I do not know the cause of the electrical issues.
AC performance tuneup times three systems. Changed out filters client supplied. Inspect blowers, evaporators and ductwork. Checked thermostats for proper operations. Verified all primary drains are clear and flowing at this time. Check outdoor units. Refrigerant levels good on all three systems. Washed condenser coil‘s. System is cooling properly at this time.
Replace evaporator door on Tam 9 air handler
remove and replace condenser fan motor and blade - parts under warranty, labor & shipping are not
Heat performance tune x 1 system. Changed out filter client supplied. Checked heat strip amp draws. Checked refrigerant levels. Tested thermostat for proper operation. System operating at manufacture specs at this time.
Upstairs unit has defected vaporator and gas temperature sensors. Need to order new and scheduled date to return. Also need to do walk through since the systems were installed at the last of January. I adjusted them to get them by until the parts come in
Homeowner has old equipment does not want to upgrade it. Also needs attic insulation and ductwork cleaning. Customer declined all repairs.
Performed A/C maintenance, refrigerant levels, run capacitors, compressor,mblower and fan motors amps were in range. Drain lines are clear. Recommended adding Reme Halo to eliminate bacteria and mode from. $995.00. Everything is working properly.
convert clean effects to 4" filter rack -
Install gas temperature sensor and evaporator temperature sensor. Also do post-install walkthrough on equipment. Systems are operating at manufacturer specs at this time.
Noise outside from the condenser. Had client turn on system and found the blade to be slightly out of balance. Advised client we would order new motor and blade for unit. System is a 17 seer with the additional coil on the inside of the condenser. Removed. And straightened inside part of the coil. Also vacuumed out leaves and washed unit. What's the thermostat to put into second stage manually. System would not kick into second stage. Zone board was not configured for a two-stage outdoor unit.