I asked for the unit to be checked to figure out why condensation was happening and why it was so humid. I was told the coolant was good and there was nothing else they could do.
Homeowner has old equipment does not want to upgrade it. Also needs attic insulation and ductwork cleaning. Customer declined all repairs.
Performed A/C maintenance, refrigerant levels, run capacitors, compressor,mblower and fan motors amps were in range. Drain lines are clear. Recommended adding Reme Halo to eliminate bacteria and mode from. $995.00. Everything is working properly.
convert clean effects to 4" filter rack -
Install gas temperature sensor and evaporator temperature sensor. Also do post-install walkthrough on equipment. Systems are operating at manufacturer specs at this time.
Noise outside from the condenser. Had client turn on system and found the blade to be slightly out of balance. Advised client we would order new motor and blade for unit. System is a 17 seer with the additional coil on the inside of the condenser. Removed. And straightened inside part of the coil. Also vacuumed out leaves and washed unit. What's the thermostat to put into second stage manually. System would not kick into second stage. Zone board was not configured for a two-stage outdoor unit.
Play neffex filtration had three red flashing lights on the door. Removed and found field charger very dirty. Advised Patrick how to clean an error code should go away. Client has a coupon for $10 off service call
deposit paid for future install beginning 1/25/2021 for 2 complete systems and ductwork, and reme halo for d/s
All systems working properly in heat mode at this time. Downstairs system has a loose manual damper in the hard duct in supply plenum rattling. Transformer is humming loudly. Upstairs system also has a loud humming transformer. Both return plenums are dirty due to age of the ducts. The compressor on both systems are pulling high amps (about 75% max). This is due to the age of the system and being heat pumps. The compressor on the upstairs system has a slight hum. Both systems are 16 seer and are 13 years old. Recommendations: -Duct cleaning both systems since duct is original - Look at replacing the R22 systems due to age and inefficiency - reme halo for allergies
AC performance tune up times two systems. Verified both drains are clear at this time filters have been changed. Inspect blower, evaporators and ductwork. Downstairs system is 425 lb low of R22. Advise client that if we added refrigerant it would not stay. Suggested replacement. Check outdoor units. Could not find Leak with my sniffer at this time. Upstairs unit is pulling 13 amps for a 3 ton unit. Both systems are 17 years old. Check capacitors and contactors. Both contractors are pitted but working. Upstairs is cooling the house at this time. Jairo to come give quote later today.
Cleaning and maintaining Trane heaters in Rockwall
Doing a 3 System A.C Maintenance in Rockwall