Professional, courteous, extremely qualified.
Jason was terrific
Joel goes out of his way to provide you with the best service possible and to make sure you are completely satisfied. Extremely knowledgeable about every aspect of the operation of the HVAC systems.
They are very knowledgeable and helpful. They were respectful, quick and on time!
Professional, knowledgeable, friendly. I’ve used this company for 20 years, never had a bad experience.
Fantastic service! Cole was very professional and knowledgeable. He took the time to explain the problem and presented the options.
No call rooftop unit. System has a wireless thermostat. It was stating that the system had lost communication. Went to Roof and found transformerDefective removed and replaced with new 75 VA transformer. System came on and operating properly at this time.
No cool. Client had let the batteries expire in the thermostat which ruined it. Removed and replaced with Trane 824 Wi-Fi thermostat. System cooling properly at this time.
Post install walk-through on recently installed equipment. Checked the units in the attic and verified both are level and drains are flowing properly. Check the thermostats for proper operations. Started up heat on both units. Check charge on units. Adjusted both systems to an 8Â° sub cool. Installed wall plate for upstairs thermostat. Systems are cooling at manufacture specs at this time.
AC performance tuneup times three rooftop units. Clean all condenser coilâ€˜s and evaporator coilâ€˜s. Toilet out all drain lines. Checked charge on all three systems. Added 2 pounds between all three systems.System is cooling properly at this time.
Could not find the problem, checked all low voltage and hi voltage connections. Have come back with Joel tomorrow. Please reschedule.
Re-strap for supplies to better access attic space. Removed return from Plenum and ran over the supplies to give extra room. The UV light for the upstairs is defective. We will call and schedule day to return with new one
Perform 2 system maintence changed both filters washed coil downstairs system is currently cooling properly. Upstairs system is low on refrigerant gave David several options he opt for letting the system run and call us later to add refrigerant and get system replacement qoute he had to speak with his wife before setting up an appointment he upgraded to platinum membership both systems
System was low on R22 freon, added 2 pounds R22. Also return filters need to be changed on all three units. Need four 20x25x2 and two 16x25x2, Misty has credit card on file.
Install attic tent downstairs attic
Arrived to install attic tent in downstairs attic access did not have the correct attic tent we will need to contact the homeowner and reschedule the attic tent install we need 1-26x65x16
Checkup on 2 trane units. Airflow was discussed and airflow correction suggestions were given to customer. Both units were washed and filters changed. Only suggestion is to have both drains redone to help with clogging will leave an estimate. Can you confirm both units are running at this time.
Arrived to find thermostat issue was the problem.
No heat. Upon arrival checked the sequence of operation and system turned on fine. Tested all voltages and amp draws on inducer, blower, board, and gas valve. Everything was within specs. Cycled the system from the thermostat to make sure I was getting proper voltage. Thermostat is sending proper signal. Checked temperature delta between supply and return and it is within manufacturers specs. System heating properly at this time.