Summertime HVAC Repair near Uptown. System was found with a clogged primary drain line. Checked the whole unit for functionality and blew out the line. Customer as well as the tenant was informed of maintenance with white vinegar or hot water being required in the future to avoid a clogged drain from happening again . System is operational.