Very pleasant to work with, from the call setting up the appointment to Brian our service tech who contacted us and arrived promptly.
Shawn called to let me know he was on his way to my house. He came in and explained what he was going to do in a polite manner. When he was finished he told us exactly what he did and that our unit was working properly.
Ambient Edge has great from the 1st call to the end, Shawn was AWESOME explained everything to us great personality and knowledgable about a range of things, I would recommend them again I'm definitely using Ambient Edge
Beau was on time, efficient and knowledgeable. He explained what work was done and why it was done at this time. He was clean and friendly. He introduced himself and said he was glad to meet us. Business was completed with a hand shake and a smile. Thank you Beau.
Shawn was very professional, and answered all our questions
Preformed clean and check on 6 year old trane heat pump Everything checked out on the unit
Performed maintenance and inspection on gas furnace. Checked all electrical components and connections and tested motors. Recorded amp draws and air temperatures
Performed maintenance and inspection on heat pump. Checked all electrical components and connections and tested motors. Recorded amp draws and air temperatures and refrigerant pressures
Upon inspection, technician found exhaust fan blade had laundry towel wrapped around it. This caused the motor to burn up and ruined the bearings. Sheaves are also worn. Recommend replacing motor, pulleys, belts, and bearings. Replaced all mentioned parts, adjusted pulley and belt tension for correct amp draw. Exhaust fan working properly at this time.
Package unit heat pump. Turned system on heat and went out side to package unit. Disconnected power to unit and removed all panels. Checked capacitor for compressor and CFM. Restored power to unit and checked amp draw on CFM, compressor and blower. Checked temp split and pressures. Cleaned evap coil. Customer changed filter prior to my arrival.
Checked system. Temp rise is good. Cleaned flame sensor. No issues at this time. Cannot renew at this time they will call when they can.
Performed cleaning check on newer Lennox split system heat pump Everything checked out on unit at this time Recommended surge protector for condenser Customer will renew EAP on next visit
Preformed clean and check on newer package Lennox heat pump Everything checked out on the unit Unit is working properly at this time
Upon inspection, technician found ECM blower motor failed. Replacing motor/module may get unit running, but we highly recommend replacement at this time. Replaced ecm blower Unit is working properly at this time Has 25 off coup
Found worn bearings in blower assembly Need fuses for disconnect Will quote