Technician Jonathon was polite, wore a mask, and quickly resolved a unique problem.
Was NOT informed that Ambiant Edge is NOT a Carrier certified repair company. Therefore my warranty is INVALID.
Shawn is the best - you should pay him more money. REALLY.
He was very good. Very informative and helpful
Plumber did a great job! He was thorough and explain what he did!
We have been a client for well over a decade. From monthly maintenance to major system repairs and replacements, they have always done an exceptional job and backed their work when things went wrong. Can't ask for more!
Found compressor and blower motor not running due to insufficient voltage being supplied to unit. Found fuses in disconnect dead. Replaced fuses and tested system operation. Everything working at this time.
8/5/2020- performed summer Pm with air filter replacement. Units currently operating as designed. Diane B
The drain pan is too short the unit tilts back away from the drain. Recommended longer drain pan and to hang unit from unistrut. Put in a repair quote sheet. Tilted the unit a little more toward drain but it is still leaking. The bathroom ceiling is badly damaged. Recommended replacing coil and condenser because the is a crack in the corner of the evap coil drain pan. Made appointment for next week for an estimate. Please call with pricing for the other recommended repairs.
Upon inspection, technician found belt close to becoming damaged. Recommend replacing belt and adding spares to each unit. 08/05/2020 Replaced belt on exhaust fan#1 and also added a spare belt to exhaust fans 1&2. Tested unit. Unit currently running as designed.
Found compressor seized, will not start. Unit already has start assist kit on it. Could not get compressor to run. Need to quote to replace compressor, unit is 11 yrs old. Recommend replacing system.
8/5/2020- arrived on property and the ac issue is from window shaker units which we do not service. Advised customer to clean filter which they do and also to wash the coil with water. No charge cancel.
Performed cooling maintenance and cleaning on split air conditioner system. Checked all motor amperages, capacitor ratings, and refrigerant pressures. Blower motor is starting to run hot. Motor may need replacement in the near future. Everything else is working well at this time. System is 20 years old and is R22 refrigerant. System should be considered for replacement in near future. Everything working at this time. Please mail invoice and estimates.
Upon compressor replacement, technician found temp control failed. This issue was not present until compressor turned on. Recommend replacing. Installed new temp control. Verified operations everything is working okay at this time. All quoted work is complete.
8/5/2020- performed summer Pm with air filter replacement. Found Economizer metal mesh filter damaged, already has a pending quote for replacement. Unit currently operating as designed.
Upon inspection, technician found all systems low on charge. Recommend adding refrigerant to systems and further diagnosing. Please note that adding refrigerant will not fix leaking systems but this will help during the summer months to keep the building cool. Adding refrigerant is a temporary solution, additional quotes may follow. Added 30lbs of refrigerant to address 57. System currently cooling as designed with discharge line temp in the 170â€™s. Added 45 lbs of refrigerant to address 55. System operating with 48 degree suction vapor at the compressor and discharge line temp in the 170â€™s. Diagnosed systems on inpatient building in same parking lot. Found one system with communication errors and one system completely flat. Will send quotes for further diagnoses and repairs.
Compressor warranty. pricing is for the labor and materials needed to do the compressor Completed all work necessary to replace compressor on reach in freezer. Tested operation. All is well at this time.
Arrived on site for customers toilet not working properly, upon inspection I noticed the float was barely allowing water to come into the tank and when they flush it it would barley go down. Made adjustments to the float allowing more water in the tank, re flushed it worked perfectly customer happy no leaks. Gonna recommend on replacement of whole toilet or a toilet rebuild. All components in the Tank are corroded and old. Customer happy no leaks.
Performed cooling maintenance on 3 split air conditioner systems. Found minor repairs in units 1 and 3. Will quote all minor repairs. System 2 found compressor plug and terminals blown out and leaked out all refrigerant. Need to replace compressor to make system operational. Due to system age and refrigerant type highly recommended system replacement.
8/5/2020- performed summer Pm with air filter replacement. Found unit 6 to have seized condenser fan motor and other fan motor over amping, quoting to replace with corresponding capacitor. Boarded up seized fan to allow for proper air flow through condenser while operating. All other units operating as designed.