I am so happy with this service, not only did they call me to tell me Chris was going to be late, when he got there we discussed what my air conditioner needed and when it needed to be done... He was completely honest with me and got me a price right away.
Mr. Sandez called us in advance of the appointment time asking if we were still expecting his visit. He introduced himself and briefly advised us of his tasks and time lines. He checked to see if we had questions or concerns we wanted addressed. He completed the check and reviewed our status for continuing services. He was very polite and personable.
Very prompt, polite, neat, quick to diagnose and helpful setting up an appointment with sales rep to discuss and compare new to old repair options. Thank you
Took the time to help us figure out where to put a new thermostat
Ambient Edge is a very Professional company and they have great qualified employees and office personal. Thank You Daniel Orozco and Zachary Obiedzenski
Good attitude, quick and got it fixed.
It doesn’t get any better than this… Ask for Ryan… Actually don’t, I want to keep him for myself. He is so good, incredibly knowledgeable with a great personality. He’s going to keep my air conditioner alive for many more years.
2 days ago tech came to maintenance unit. Tech changed out dual capacitor. Customer said that tech recommended cfm replacement and the customer agreed. Customer stated that tech informed him he didnâ€™t have the correct motor on his van at the time and that the office would call him to set apt to change motor. The call is considered a call back so I didnâ€™t charge for the dispatch fee. Replaced bad cfm and restored power to unit. Verified proper operation of the unit. Unit on and working properly at this time. Please cancel and future apts to replace cfm.
Arrived on site and ran 1/2 black steel gas / gas track pipe from the roof to the dryer, installed a 2 foot riser out of roof flashing and installed a gas valve, flex lined into the 1/2 gas tee. Transferred black steel pipe to track pipe in addict and installed clamps to the up rights for support installed a riser from addict to appliance with a sediment trap. Put 13 psi at 530 for leak check. Bubble checked every connection for leaks. No leaks found will call for inspection. Customer happy up to code.
Upon arrival found that the unit was running and cooling. The problem that was found was that the â€œupâ€ and â€œdownâ€ button was unable to move the set point on the thermostat. I installed a t4 thermostat and tested it to make sure it would satisfy in heating and cooling. Unit is currently running and cooling.
Performed maintenance and inspection on air conditioning. Checked all electrical components and connections and tested motors. Recorded amp draws and air temperatures and refrigerant pressures. Unit is 20+ yrs old r3commend replacement
4/9/21 upon arrival found unit off at thermostat tested thermostat operation and the unit turned on. Found blower capacitor tested out of range, also found condenser motor casing extremely hot and coil dirty. Was able to clean coil, checked unit charge- found slight restriction and also found a suction line filter drier in system. Advised customer this does not stay in the system and has a potential to restrict refrigerant flow when clogged. Due to age,condition and phased out R22 advised against repairs and noted system replacement Would be the best option. Customer agreed but at this time unit was cooling and customer agreed to replace old mercury thermostat. Tested new thermostat in heating and cooling and is operating properly.
Customer stated that he will have someone else do work and rejected service at door
Preformed clean and check on 15 year old Trane unit Blower motor is running warm Everything else checked out on the unit Unit is working properly at this time Collected check would not process
Cooling maintenance Split system Went to thermostat and turned system on cooling. Went to condenser and disconnected power to unit. Removed panel from condenser and checked capacitor for CFM and compressor. Restored power to unit and checked amp draw on CFM and compressor. Checked temperature split and refrigerant pressures. Went to air handler and disconnected power to unit. Checked drain lines and duct work. Checked capacitor for blower. Restored power to unit and checked amp draw on blower. Replaced bad blower capacitor
Performed cooling maintenance with coil cleaning. Unit currently running as designed. I found that the compressor contactor is showing signs of pitting and should be replaced soon. Also unit is over 10 years old so I recommend replacement.
Arrived on site, used camera to inspect main septic line, found what looked to be a clog in 4â€ pipe, used snake to clear clog, ran camera again to check line and further down the line the septic tank seems to be backed up into the tank inlet meaning the tank is full, customer will call a septic company and the pipe itself was in great condition no repairs needed
Disconnect and abandon old lineset, install and connect new lineset to system, pressure test for leaks, evacuate system, recharge system using customer supplied refrigerant, added AC Renew to system, ran and tested operation. Everything working normally at this time. Customer signed up for EAP for fall2021/spring2022
Upon arrival found condenser fan motor failed. System is old and is r22. Contactor is burnt. Due to age and condition of system highly recommended replacement soon. System is down at this time. No further action at this time per customer choice.
3 ton packaged Bosch heat pump on roof with crane Aero seal Honeywell 8000duct cleaning system surge 10 year parts and labor warranty
Removal of existing faulty water heater and installing new unit and bringing up to code, arrived on site to install new 6 year 40 gal electric water heater disconnected water to property and turned breaker off to water heater from breaker box rolled existing 50 gal water heater out of garage after disassembleing wire connections and existing supply lines knocked drain plug off drained into street unsweated existing ball valve put 3/4 Sb ball valve with an Sb threaded adapter installed threaded adapter on outlet side of copper installed New supply lines and expansion tank assembly turned water back on to property filled tank wired up new unit after filling completely turned breaker back on all approved work complete customer satisfied.